Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
pulled charge back into condenser unit. Removed old evaporator coil. Installed new evaporator coil and adapted to condensation piping and exahaust piping. Brazed in listen and pressure tested at 340 psi nitrogen. No leaks found. Vacuumed System down to 380 microns. Tested condensation drain with water. Checked temperature split at indoor unit had a 19 degree temperature split. R 410a pressures were 322/117 with 7 subcooling. Systemz