Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Recently installed boiler not producing hot water or heating for the home, upon arrival found boiler on code D3, check water pressure and reading 15 psi, released some water so low water cutoff would reset, also during process noticed back side for low voltage connections, t t were not making good contact, repaired low voltage connection....check for operation ok boiler is working within specifications
Arrived at customers home and checked boiler for why it is not heating. Found code d3. d3 code is low water cutoff. Purged air out of system. Small air pocket trapped at LWCO. Ran system for an extended period of time and no more code. Heating home nicely. Initially automatic water feeder not feeding water automatically. Made adjustments and now is working and holding pressure at 15psi. Performed Quality Assurance inspection on a newly installed gas high efficiency boiler. Checked over entire system. Checked programming. Everything is proper and correct. Venting proper and good pitch. Checked for water leaks. No leaks present. No gas leaks. System running great when I finished. System looked really good.
Drained and removed old hot water heater and boiler. Installed new Bosch combi boiler. Installed new zone valves, circulator pump, air eliminator, shutoff valves, gas piping, condensate pump and vinyl, water cop main shutoff, and ran new flue piping. Installed 2 new thermostats. Filled purged and tested boiler and hot water heater. Tested combustion and pump. System working great at time of install.
Review and prep for upcoming boiler install