Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Precision AC Tune Up: 3.5 Ton Amana AC system. Temp split ok. Replaced filter. Drain and trap ok. All feild/manufacturers wiring ok. Outdoor voltage/compressor amps indoor amps ok. Refrigerant pressures/subcooling/superheat ok. Both coils are in good condition. System is operating well at the time of this tune up.