Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Reconnected 2 condensers and pressure tested. Then evacuated down to 250 microns. Released refrigerant and adjusted charges. Reconnected high and low volt. Secured disconnect back to wall. Both units had near 20 degree splits. Systems working well. Added 1lb to Goodman unit.