Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed gas heat check up check electrical low and high ok replace high efficiency filter and also replace humidifier and serviced as well, test humidifier and set to winter 35% check feed tube for water flow, ok clean sensor and check burners gas pressure ok combustion test cycle heater ok test pump ok
No heat found heater locked out on pressure switch, clear tubing and exhaust fan, cycle heater and test ok during same visit performed gas heat inspection check electrical low and high ok replace filter check gas pressure combustion test ok cycle heater ok replace blower cap customer ok with price supply air 117 rerun 70
Performed propane gas heater tune up check electrical low and high ok filter ok check burners and smart gas valve operation ok gas pressure ok combustion test replace blower cap reading below rating, customer ok repairs, cycle heater ok
Performed gas heat inspection check electrical low and high ok replace filter, cleaned sensor and check burners ok gas pressure ok test all safeties ok limit, pressure switch and door switch ok performed a combustion and efficiency test ok cycle heater ok would recommend installing a whole house humidifier
When we arrived found blower on old indoor oil furnace constantly running. Pulled off Nest thermostat from the wall and still continued to run. Removed g terminal wire from sub base and it still was running. Went down to furnace and found there was an open limit in the blower compartment. Jumped limit out and it still continued to run. Pulled g wire from control board and still running. Bad relay on fan timer board. Also while in blower compartment found squirrel cage bent and shaft to blower moter had wobble in bearings. After talking to homeowner, he is not fixing anything at this point. He would like to switch over to propane. He is going to just let it run as is at this point. Homeowner would like a quote to install furnace , he will call when ready.
No hot water, pilot not stay lit, found defective thermocouple quoted for new thermocouple customer ok replace thermocouple and test water heater cycle water heater ok
Performed ac check up check electrical low and high ok replace filter 20x20x1 check split supply 49 return 66 no load inside the house, blower cap ok check outdoor unit 410 pressures ok capacitor and contactor ok cycle unit ok pressures 200/90 with 9 sub cooling and 25 superheat outdoor temp is 70 inside temp is 66 no load in the evaporator, test pump couldnâ€™t flush drain no excess port to drain
Performed ac check up, check electrical low and high ok flushed drain test pump ok replace 413 filter, check split outdoor unit 410 pressures, check capacitor and contactor ok coil is clean cycle unit ok
Performed ac tune up, check electrical low And high ok check filter, flushed drain ok check split ok outdoor unit 410 pressures ok capaand contactor ok coil is clean cycle unit ok
Performed 6 month ad and heat inspection. Check electrical low and high ok flushed drain test pump ok replace 413 filter, check low and high stage gas ok combustion test ok check outdoor unit 410 pressures ok capacitor and contactor ok
No heat, found heater off upon arrival, start heater and check operation, heater would ignite then shutdowns, found defective flame sensor, also installed new air filter, and a well as new blower 5 mfd, due to very weak only reading 3 mfd, after all repairs, test unit ok cycle ok combustion test ok HIGHLY RECOMMEND REPLACING AIR FILTER ONCE EVERY MONTH
Removed water heater . We had to disconnect the gas , high voltage and condensate piping from furnace to get the water heater out of the closet. Installed new 40 gal natural gas water heater . Reconnected hot and cold water pipes . We installed a new ball valve for the water heater . The shut off before was in the back and very hard to get to . Now itâ€™s in the front and ez access. We reconnected gas and exhaust pipe to the water heater . We bubble tested the gas line . We reconnected condensate pipe , gas pipe with bubble test and high voltage to the furnace. The furnace off and on switch was cracked at the back of the switch so I replace the switch with a new one . Tested both furnace and water heater and both were running to standards. I would recommend the furnace to be serviced due to the age of the equipment and the last time it was serviced.
Recommend replacing primary control,,,,,,,replace combination primary/transformer with new ignition transformer and new primary control, also installed new cad cell, adjust settting to delay valve to 10 seconds, cycle and test couple times ok stars with no problem, cad cell reading 90 ohms, test limit ok, when opens cuts 115 volts to burner,
Upon arrival found Carlin combination primary/transformer locked out, check T T STATUS closed, check 115 volts to combination pri/trans ok getting 115 to tried to reset but was not able to reset,,,finally was able to reset, check cad cell reading 600 ohms, put in new cell temporarily for testing purposes reading 160. Primary went on locked out during testing, and couldn't reset it, would hold reset button for over 1 minute but still not resetting recommended replacing primary control ,,,,
Installed a new amana outdoor unit on a new pad. New disconnect and whip were also installed. Inside we installed a new amana gas furnace with an amana coil on top. We adapted the existing supply plennum to the new coil. Installed air cleaner onto the return. We tied the gas piping back in and adapted the flue piping to the new coil. Ran a new condensate drain and installed a new EZ trap and new condensate pump. Both the ez trap and the new pump are wired to the unit. Ran new vinyl tubing to the sewer where the old one was ran. Flushed and pressure tested the line set and pumped down the system. We tested in heat and cool and the system is running to factory standards.