Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Dibiase did a wonderful job. Very respectful about our home and took the time to explain everything in detail. They were also very realistic about the best fix for the situation. I never felt like they were just trying to sell me something. Highly recommend, 5/5 stars!
Performed heater certification of American standard 80% gas furnace. Homeowner just replaced 213 air filter. Checked all electrical conections and components. Checked temperature rise. Found some moisture on smoke pipe wiped of piping and inside furnace. Found bad 115 volt condensation pump, homeowner to replace. Performed combustion test. Cleaned flame sensor. Gas furnace is working fine at time of inspection.
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, and Amana condenser. Ran new lineset and brazed in with nitrogen. Installed new Aprilaire high efficiency air filter. Installed new Amana high efficiency gas condensing furnace. Placed new coil on top and brazed in with nitrogen. Pressure tested to 300 psi and evacuated down to 135 microns. Fabricated a plenum and sealed all ductwork. Reconnected gas and leak checked. Converted furnace to propane. Installed new ez trap and pump and ran condensate piping. Ran new vinyl to discharge. Reconnected venting and added fresh air drain. Installed new receptacle and switch and reconnected electric. Wired in low volt. Installed new t10 thermostat. Tested all functions. Performed combustion test and adjusted gas pressures. Charged unit to specifications. System running great at time of install.
Found lp gas furnace hot surface igniter coming on and lighting pilot but not lighting main burners. Did not hear any click at gas valve during a call for heat. Checked lp gas pressure with a digital manometer , had 11.1 w.c. Up to valve and nothing coming out of valve, bad gas valve. Gas valve is a Honeywell smart valve . Recommend replacing both gas valve and control board. Both board and smart valve would cost around $1500 to replace. Also found heat exchanger has a lot of rust and corrosion. Recommend to replace furnace and a/c together due to being 15 years old. Homeowner will call us to talk about replacement.
Performed precision heat tune up on amana gas furnace. Replaced 20x25x1 air filter. Checked all electrical conections and components. Cleaned flame sensor. Blew out condensate drain. Checked temperature rise. Checked gas pressure and performed combustion test. System is working fine at time of inspection.
Performed two ac check ups, check electrical low and high ok both filters ok, 16x25x1 both, check blower motors and caps, caps reading below ratings, check temp split on both units, first floor running at 18 split second floor 13 split, check outdoor units refrigerant pressures r22, second floor is slightly low on refrigerant, first floor unit r22 pressures ok, informed customer about second floor unit, both furnaces and ac units are from 2003 average life expectancy is between 10 to 15 years, both units have passed the average life expectancy from manufacture
Performed ac tune up check electrical low and high ok filter ok check drain seems to be ok traps does not have access to clean trap check temp split blower motor and cap ok outdoor unit refrigerant pressures ok replaced capacitor and contactor cycle unit ok
Performed ac tune up check electrical low and. High ok replace air filter, check drain ok check temp split only 11 degree split check ref charge 200/70 with 18 sub cooling and 26 super heat txv as meter device, thermal expansion valve not opening correctly check capacitor and contactor ok cycle unit
Performed Precision AC Tune Up on Heat Pump system. Found 16x25x1 Air Filter very dirty. Also found a second Fiberglass filter in the return box. With the Dirty filter and the second filter system was not getting enough Airflow and refrigerant levels were dropping to below freezing on the indoor coil. Recommend checking Filter every 30 Days and using a filter that does not exceed a MERV rating of 8. Inspected electrical components on indoor and outdoor units. Cleaned drain line and pump. Filled pump basing and tested operation. Measured refrigerant charge on system. System has slightly higher Subcooling and superheat levels and may be overcharged. System is operating within normal Amp and Voltage ratings.
Performed cooling maintenance on 2 air conditioners, replaced standard air filters. Cleaned condensate pan and drain. Checked voltage, amperage and electrical connections, measured capacitor values, replaced first floor furnace run capacitor. Started air conditioners, checked refrigerant charge, found second floor air conditioner low on charge. System is R22 recommend replacing system vs repairs. Need to quote to replace second floor system.
Performed ac tune up check electrical low and high ok filter ok flushed drain ok check blower and airflow ok outdoor unit refrigerant pressures ok capacitor and contactor ok installed super boost to compressor to improve start ups, compressor starts with more torque and less power consumption, also during visit performed a water test found water to be 14 grains and chlorine Levels just above normal emailed proposal for water treatment system
Performed ac tune up check electrical low and high ok replace filter 413 flushed drain test pump ok check split check outdoor unit refrigerant pressures capacitor and contactor ok coil is clean cycle unit ok
Performed heating maintenance, checked media filter ok. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test and checked temperature rise.
Performed gas heat check up check electrical low and high ok replace high efficiency filter and also replace humidifier and serviced as well, test humidifier and set to winter 35% check feed tube for water flow, ok clean sensor and check burners gas pressure ok combustion test cycle heater ok test pump ok
No heat found heater locked out on pressure switch, clear tubing and exhaust fan, cycle heater and test ok during same visit performed gas heat inspection check electrical low and high ok replace filter check gas pressure combustion test ok cycle heater ok replace blower cap customer ok with price supply air 117 rerun 70
Performed propane gas heater tune up check electrical low and high ok filter ok check burners and smart gas valve operation ok gas pressure ok combustion test replace blower cap reading below rating, customer ok repairs, cycle heater ok