Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service call that the Gas Boiler was not working and was not Heating the Home. Upon arrival, spoke with Homeowner about issue. Found Thermostat set to Heat at 66 Degrees with an indoor Temperature of 55 Degrees. Proceeded to the Boiler to troubleshoot. The Boiler was not in operation and after troubleshooting found that their was not Power going to the Boiler. Found the Emergency Shut Off Switch at the Top of the Basement Steps was Turned Off. Turned Switch on and Boiler began operating. Performed Precision Heating Tune Up on Boiler. Disassembled and cleaned Heat Exchanger and Ignitor Assembly. Clean Boiler Drain Line and Condensation Pump. Inspected Electrical Connections. Tested Expansion Tank to ensure Air Pressure was present. Performed Combustion Analysis on Modulating Boiler. Monitored operation of Boiler to ensure it was Heating properly and the Radiators were getting hot.