Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision Heating Tune Up on Gas Fired Ultra Boiler. Cleaned Drain Line and Condensation Pump. Disassembled Heat Exchanger and cleaned. Cleaned Flame Rod and Ignitor. Tested Expansion Tank for Air Pressure. Put system into operation and performed Combustion Analysis. The Radiant floor Heat was in operation but the radiator heat for the whole house had not been turned on yet this season. Checked radiators to ensure they were getting hot. Boiler was still running to get up to water Setpoint but Supply and return water temperatures were within the 10-12 Degree standard of each other.q Would recommend during next heating tune up to replace the Gaskets on the Boiler using the Weil McLain Kit which includes new Gaskets and Flame Rod Assembly for Boiler. Included an estimate for the Gasket Kit.