Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service call that the AC was shutting off intermittently. Spoke with Homeowner about issue who informed me that a home warranty company had previously found the Condensation Pump shutting down. Filled Condensation Pump to test Operation. Pump motor initiated but was not able to discharge any water. Disassembled Pump and found that it was extremely dirty and clogged. Due to condition recommended new Condensation Pump. Installed a new 115V Pump and wired in the Safety Overflow Switch. Blew through the Vinyl Tubing which is very dirty looking. Tested operation of Pump multiple times to ensure it was pumping out. Currently Pump is discharging the water outside. With the condition of the Vinyl Tubing, and the Humidifier Recommended replacing Vinyl Tubing and rerouting to a Pipe inside. This will prevent the Tubing from freezing in the winter and the Tubing clogging due to its current poor condition. Also spoke with Homeowner about the Blower Motor Capacitor testing below rating, and the H