Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision Heating Tune Up on Gas Furnace. Replaced High Efficiency 201 Filter provided by the Homeowner. Cleaned and tested Humidifier. Opened Dampers and set Humidistat Control to 35%. Blower Motor Capacitor was testing below rating. Installed a new 5 Mfd Capacitor and tested operation of system. Performed Combustion Analysis on Furnace and measured Air Temperature readings. Vinyl tubing for the Condensation Pump is very dirty. Vinyl Tubing is also ran to the outside of the Home. With the Humidifier Draining into the Pump that has the potential to freeze. The Condensation Pump filled and pumped out while testing system. However, would recommend running new Vinyl Tubing to an inside discharge point. System is about 21 Years old. Due to age of system, would recommend to begin planning for replacement of the Gas Furnace/AC before any issues or failure occurs.