Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Checked no cooling complaint, checked air filter ok. Started air conditioner, air conditioner started and runs, checked temperature drop across coil, found only a 8 degree drop. Checked refrigerant charge, found low on charge. Topped off refrigerant charge and balanced by superheat. Checked operation and temperature drop across coil. Recommend replacing system due to age and obsolete R-22 refrigerant. Home warranty company to repair or replace system.