Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision PECO Heat Tune Up on system. Replaced the 16x20x1 Air Filter. Inspected Indoor and Outdoor Coils. Coils were clean and did not need a cleaning. Inspected Blower Motor and Blower Motor Bearings. Motor is an encased motor and no lubrication was needed. Inspected Electrical Components on Air Handler and Outdoor Unit. Dual Capacitor for the Outdoor Unit is testing below rating on the Fan Motor Side. Recommend replacement of the Dual Capacitor before damage to the Outdoor Fan Motor occurs. Measured Refrigerant charge in Heating Mode and verified refrigerant charge with Manufacturer charging chart. Tested Auxiliary Heat Kit on system. Completed PECO Checklist Form in system.