Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Precision AC tune up for 2 Ton Amana communicating AC system. Replaced filter. Cleaned EZ trap and tested/verified drain. 18F temp split. Refrigerant pressures/subcooling ok. All electric motors and components ok. Compressor amps/indoor Amps/outdoor voltage ok. All field and manufacturing wiring/connections ok. Both coils are in good condition. System is operating well at the time of this tune up.