Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service call that AC was not cooling. Upon arrival spoke with homeowner about issue. Turned system on and found the Outdoor Unit was not running. Tested components and found failed Dual Capacitor. Replaced 50/7.5 Mfd Capacitor and put system in operation. Head pressure was elevated on system, and Subcooling levels is elevated. Rinsed outdoor coil with water to ensure it was clean. System appears to be overcharged. System is cooling, but Amp draw is higher, but still within rating. Replaced 16x25x1 Air Filter. Tested Blower Capacitor which is below rating. System is a builder grade a Nordyne/Gibson system that is about 13-14 years old. Due to age and overall poor condition, would recommend begin planning for replacement of system. Included estimates for the installation of Hard a Start Kit for Outdoor Unit. Would also recommend having system maintenanced in the Winter and Summer. System does not appear to have had maintenance performed.