Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service was great, on time and Luis is very helpful and professional.👍
Knew what he was doing and had a lot of great info to share.
Performed ac tune up, check electrical low and high ok filter ok flushed drain test pump check temp split ok outdoor unit 410 pressures contactor and capacitor ok cycle unit ok
Performed ac check up check electrical low and high ok check filter customer supplies filter 16x25x1 check and flushed drain test pump ok split ok outdoor unit 410 pressures ok contactor and capacitor ok cycle unit ok
Performed gas heat boiler, check electrical low and high ok clean flame sensor/igniter, flushed trap and fill with water once it was clean, test all two zones ok, combustion test cycle boiler ok water pressure at 15 psig, expansion tank ok, check inputs and outputs ok all temps ok,
Performed quality assurance inspection on system. All looked good.
Replaced air conditioning unit and air handler new pad whip disconnect new linesets new pan and wet switch. Added new supply plenum and reconnected all the supply hits re ran return from 14 to 16 inch using same central return 30x30x1 filter completed set up and installation went over thermostat with customer new thermostat as well need to return and install 30 amp breaker
Check system operation, did not replace breaker, found size wire 12/2 canâ€™t replace breaker with bigger, currently has double Pole single throw square D QO breaker 20 amp, recheck operation system ok, tightened all connections there was loose connection on one side, that could of been the problem, we would check system during the 6 month inspection
Performed Walkthrough of jobsite to size and measure location for upcoming installation. Completed Wells Fargo Financing paperwork with Homeowners while onsite.
No hat, no 24 volts, noticed 5 amp fuse blown, open, check outdoor high pressure switch wire, made repairs and test unit ok, cycle heat pump. ok,
Performed oil heat tune up, check electrical low and high ok clean exchanger and flue pipe, replace oil rf-1 and .60x70B nozzle clean and adjust electrodes ok flame detector ok check oil flow and pressure ok smoke test ok combustion test cycle furnace ok check draft ok also service humidifier new pad test ok set to winter 35%
Performed heat pump check up check electrical low and high test back up heat ok 10 kw new filter, check outdoor unit 410 and electrical ok test defrost cycle heat pump ok system up to standards
Replace blower motor due to failure test and cycle indoor and outdoor unit ok
During repair on next door unit, noticed heat pump cycling on and off, check operation unit going off on high pressure, blower motor not working, check wiring ispect module, motor getting 257 volts and 24 volts for module, motor need to replace also recommended adding x13 motor protector to this unit and all units in the building due to high voltage coming in incoming voltage is 258...unit rated at maximum of 253 volts
Repair leak, evacuation and charge system by super heat at and subccoling, added 8 lbs 410-A check super hat and subccoling ok, system ok 6 super heat and 7 subccoling 390/130 indoor temp 72 and outdoor temp 62 outside recommend adding x13 motor protector and outdoor surge protector due to high voltage exceeding 253 volts
Add nitrogen to system and find leak, further work needed after finding where system is leaking, gout be joint, coil or copper line, after we find leak we would be able to give price to repair, add nitrogen to system and look for leak, found true suction ,,,leaking, need to solder and pressure test unit, (leak generated from manufacturer joint, near reversing valve over time vibration,) need to return visit to performed repairs vacuum pressure test and charge system, also when working on unit, on 4231 outdoor unit snow legs are fallen apart installed bricks as temporary fix, but new snow legs should be installed,
Performed oil cleaning on furnace clean heat exchanger and flue pipe, clean chimney base, almost blocked with tree leafs and small branches, clear and clean chimney base, replace nozzle and oil filter, .75x80b and rf-1 check for leaks no leaks, smoke test and combustion test new air filter cycle furnace ok