Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Pleased with technicians work and he is a nice guy
Service was great, on time and Luis is very helpful and professional.👍
Knew what he was doing and had a lot of great info to share.
Removed old cast iron baseboard. Replaced with new fin and tube baseboard. Began filling loop and noticed another leak at a coupler in crawl space. Was able to solder connection back on. Began filling system again and found another leak at cast iron baseboard in second bedroom. Will get back to customer with quote. Left loop off and purged other side. Balanced system so far radiator heats evenly.
Performed heat pump check u check electrical low and high ok replace air filter, check back up 7.5 electric heat ok check split ok outdoor unit 410 pressures ok capacitor and contactor k test defrost ok noticed water heater leaking at the hot side outlet top discharge took pictures would recommend replacing water heater emailed quoted for new 50 gallon electric
Removed old boiler and piping. Installed new Weil McLain ultra oil boiler. Installed 2 new taco ecm circulators. Installed new supply and return piping up to existing cast iron piping. Installed new flu piping. Installed new oil filter and line. Installed taco zone panel. Found leaking baseboard on zone 2. Valved off and ran and tested on zone 1 only. Tested combustion and boiler operation. Boiler is running great at time of install.
Performed heat pump check up check, upon arrival found unit not working thermostat calling for heat but unit not running, found no 24 volts on terminals, open fuse, check all wiring ok, replace fuse and test unit check indoor and outdoor wiring ok no issues found, check electric heat back up ok new filter, check outdoor unit 410 pressures ok capacitor and contactor ok test defrost ok no Shorts were found all components and wiring checked out ok amp draw on red hot side of low voltage transformer is .4 amps on y goin to outdoor heat pump .2 amps
Oil furnace not working, we did tune up yesterday now no heat, found clogged nozzle, quoted for new nozzle customer ok repairs, replace nozzle and cycle furnace couple time ok
Performed oil furnace tune up, check electrical low and high ok cleaned heat exchanger and flue pipe, check air filter ok, replace oil filter and installed new nozzle, check pump pressure 155, clean and adjust electrodes, cad cell is clean, cycle furnace and performed smoke test and combustion test ok
Performed heat pump check up check electrical low and high ok check 5 kw back up ok filter ok check split outdoor unit 410 pressures capacitor and contactor ok both coils are clean test reversing valve ok also performed oil furnace tune up check electrical low and high ok clean heat exchanger and flue pipe, replace nozzle and electrodes also replace oil filter and adjust air ratio performed smoke test and combustion test cycle heater ok cycle both units ok
Upon arrival found boiler locked out, high temp lock out, test boiler check water pressure ok 17 psi check inputs and outputs check all three circulators ok noticed some air in the pipes, bleed all air from inside pipes check operation domestic and regular house heat ok temps not getting oblige limit, also noticed boiler lost power and lost its settings memory reprogram settings and pre and post purge to manufacturer recommendations second floor thermostat needs new batteries only first floor was able to test,
Performed ac check up, on a heat pump check electrical low and high ok filter ok check split, outdoor unit 410 pressures capacitor and contactor ok Chelsea unit ok supply temp 56 return 77
Performed ac check up, check electrical low and high, check filter ok check split, blower cap ok flushed drain test pump ok outdoor unit r22 pressures, capacitor ok contactor shows some black burners in contacts, cycle unit ok
Performed ac check up, check electrical low and high change filter, flushed-drain test pump ok check split ok outdoor unit 410 pressures capacitor and contactor ok cycle unit ok noticed round ductwork not insulated and sweating recommended attention
No ac, oil furnace blower runs, but no outdoor unit, found burnt wires on common side on capacitor replace wires and connotations cycle and test ac unit, due to age and condition system should get replace Office will get in contact to schedule visit for pricing on a new oil furnace and new ac unit quoted to repairs electrical connections customer ok cycle and check r22 pressures ok 200/75
Checked no cooling complaint, found outdoor not running, found open dual run capacitor. Replaced run capacitor. Started air conditioner, checked operation and amp draw ok.
Performed ac tune up, check electrical low and high ok filter ok flushed drain test pump check temp split ok outdoor unit 410 pressures contactor and capacitor ok cycle unit ok
Performed ac check up check electrical low and high ok check filter customer supplies filter 16x25x1 check and flushed drain test pump ok split ok outdoor unit 410 pressures ok contactor and capacitor ok cycle unit ok