Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Five years ago, I never heard of this company, my heater died on the coldest day of the year and I called everyone that I had seen advertised on TV and no one would come out. Someone gave me this name and they were here in a heartbeat. Same thing happened with my AC going out on the hottest day this year, and guess who was here in a minute. Really, when you're freezing or too hot to even think and your system has a problem, there is nothing more important than knowing someone will be here to help. That is this company!
Luis was great. Thanks for sending him
Service Technician was on time, very nice, professional and completed work required. Very pleased.
Pleased with technicians work and he is a nice guy
Service was great, on time and Luis is very helpful and professional.👍
Replaced blower motor, blower relay, motor wiring harness , and t-4 thermostat. Cycled on heat pump system in heating mode. Outdoor ambient air temperature is 46 degrees. 410a refrigerant pressures in heating mode are 291/103. Checked temperature rise in heating mode and it was exactly 20 degrees. Had Eric from hvac check over everything. We jumped out the indoor fan motor at wiring strip from rot g terminals and r to w terminals. Heat pump is cycling on and of correctly at time of service.
Performed heat pump tune and also oil furnace cleaning, check electrical low and high ok replaced both filters, check back up heat on heat pump, temp rise outdoor unit refrigerant pressures ok test defrost ok cycle heat pump ok. On oil furnace cleaned flue pipe heat exchanger and replace nozzle, oil filter, performed smoke and combustion test unit is working at the time of service cycle both units ok
Replaced blower relay with newer style relay. Call tech support to let them know the procedure that is being taken. Checked electrical conections on new core sense. Cycled heat pump threw emergency heat, heat pump heating, and cooling mode. Blower is coming on at the appropriate times. Let homeowner know that we are going through the steps to find out what is causing these lock outs to occur and to keep us informed if any new situation occurs.
Performed oil furnace tune up cleaning, clean heat exchanger through exchanger clean ports, and tried to clean as much as possible from rear flue. Very hard to removed flue, replace nozzle pump strainer and oil filter, performed smoke and combustion test ok check temp rise supply 120 rerun 73 cycle furnace ok
Customers thermostat has lost power, check 24 volts on air handler and at thermostat found 24 volts preset, check electric back up heat ok check outdoor unit and found burnt components on the outside heat pump, took photos os condition recommend replacing heat pump we will come out tomorrow to provide options to customer
After talking to homeowner about issue, he had mentioned that about 2 nights ago he had noticed the outdoor heat pump running, but not the fan at the indoor blower. Put gauges on system and got homeowner to give a call for heating. Called tech support and gave them model and serial numbers of indoor and outdoor heat pump. Had pressures ind heating mode at 68 degrees of 326/123. He wanted me to check the super heat in heating mode and verify static pressure. Static pressure was .5 w.c. . And had a super heat after 15 minutes of run time of 9.8. He had mentioned that possibly the ice cube relay inside the air handler was not picking up the fan, but homeowner said he had no issues in cooling mode. Told Phillip to keep any eye on it and give us feed back if he notices outdoor unit running with out the indoor blower,
No ac found outdoor unit locked out on code 2 compressor issues, check capacitor ok fan motor or ok reset unit and ran on heat and cool mode test defrost ok refrigerant pressures ok, air filter ok blower motor ok, would recommend a maintenance visit some time this fall or winter to double check unit, core sensor might have internally failed and may need to be replaced if same issues occurs
Performed gas heat tune up check electrical low and high ok replaced air filter, cleaned flame sensor, check burners ok check blower cap and motor ok, gas pressure ok combustion test cycle furnace and check supply and return air 135/73 system is working little harder to keep up with load
Performed oil heat tune up on furnace, check electrical low and high ok check air filter ok, clean heat exchanger and flue inspect and clean chimney base ok replaced nozzle, oil filter and pump strainer, noticed electrodes are flat at the ends, would recommend replacing them, clean flame cad cell cycle burner ok performed combustion and smoke test cycle furnace ok emailed proposal for electrodes replacement
Customer has questions about ductwork, and also blower too loud, oil furnace, with btu Input of 120, system has central return, found two filters on unit both were super dirty, also noticed furnace cycles on high limit, did noticed blower is very loud when it comes on, did not find any issues with blower, what I would recommend is having furnace clean/tune up and lower nozzle size to lower the btu input and then we can see if we can lower blower speed, also other option is to replaced furnace with low profile and high efficiency blower, emailed service plan information for oil furnace
New customer, reason of call to perform gas check up, Upon arrival found furnace off, pilot was out, standing pilot, relight pilot and performed combustion test, furnace is running at over 1000 co ppm, furnace is from 1987, poor shape and very unsafe to use, carbon monoxide can leak into home, informed customer that current condition of furnace is very dangerous and shOuld not be in operation, turned pilot off and declared furnace unsafe to operate, customer needs to replace furnace
Drain Down, Disconnect, and remove existing Water Heater. Install a new 65 Gallon Rheem Hybrid Heat Pump water Heater in Auxiliary Drain Pan with Alarm. Adapt Hot and Cold Water Pipes to new Water Heater. Install Condensation Drain Piping for Water Heater. Complete Electrical Connections to Water Heater. Fill Tank and purge lines of Air. Setup Water Heater Programming and put into operation. Complete Water Heater Installation Checklist in system upon completion.
Performed heat pump check up check electrical low and high ok replaced filter 16x25x1 check blower compartment and coil ok test 7.5 kw back up heat ok check airflow outdoor unit refrigerant pressures ok capacitor and contactor ok test defrost ok cycle unit ok emailed proposal for water heater replacement with hybrid water heater
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system. All penetrations sealed, wiring secure and proper. System running great at time of QA.
Reclaimed and removed old ac ,coil and heater. Installed a new amana gas heater with amana coil on top . Adapted all metal as needed and taped and sealed all joints. Ran new copper lines brazed and leak checked. Installed an new condensate drain with a ez trap wired in and new pump and vinyl tubing. T4 stat. Tested unit and itâ€™s running good .