Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service was great, on time and Luis is very helpful and professional.👍
Knew what he was doing and had a lot of great info to share.
Upon arrival found boiler locked out, high temp lock out, test boiler check water pressure ok 17 psi check inputs and outputs check all three circulators ok noticed some air in the pipes, bleed all air from inside pipes check operation domestic and regular house heat ok temps not getting oblige limit, also noticed boiler lost power and lost its settings memory reprogram settings and pre and post purge to manufacturer recommendations second floor thermostat needs new batteries only first floor was able to test,
Performed ac check up, on a heat pump check electrical low and high ok filter ok check split, outdoor unit 410 pressures capacitor and contactor ok Chelsea unit ok supply temp 56 return 77
Performed ac check up, check electrical low and high, check filter ok check split, blower cap ok flushed drain test pump ok outdoor unit r22 pressures, capacitor ok contactor shows some black burners in contacts, cycle unit ok
Performed ac check up, check electrical low and high change filter, flushed-drain test pump ok check split ok outdoor unit 410 pressures capacitor and contactor ok cycle unit ok noticed round ductwork not insulated and sweating recommended attention
No ac, oil furnace blower runs, but no outdoor unit, found burnt wires on common side on capacitor replace wires and connotations cycle and test ac unit, due to age and condition system should get replace Office will get in contact to schedule visit for pricing on a new oil furnace and new ac unit quoted to repairs electrical connections customer ok cycle and check r22 pressures ok 200/75
Checked no cooling complaint, found outdoor not running, found open dual run capacitor. Replaced run capacitor. Started air conditioner, checked operation and amp draw ok.
Performed ac tune up, check electrical low and high ok filter ok flushed drain test pump check temp split ok outdoor unit 410 pressures contactor and capacitor ok cycle unit ok
Performed ac check up check electrical low and high ok check filter customer supplies filter 16x25x1 check and flushed drain test pump ok split ok outdoor unit 410 pressures ok contactor and capacitor ok cycle unit ok
Performed gas heat boiler, check electrical low and high ok clean flame sensor/igniter, flushed trap and fill with water once it was clean, test all two zones ok, combustion test cycle boiler ok water pressure at 15 psig, expansion tank ok, check inputs and outputs ok all temps ok,
Performed quality assurance inspection on system. All looked good.
Replaced air conditioning unit and air handler new pad whip disconnect new linesets new pan and wet switch. Added new supply plenum and reconnected all the supply hits re ran return from 14 to 16 inch using same central return 30x30x1 filter completed set up and installation went over thermostat with customer new thermostat as well need to return and install 30 amp breaker
Check system operation, did not replace breaker, found size wire 12/2 canâ€™t replace breaker with bigger, currently has double Pole single throw square D QO breaker 20 amp, recheck operation system ok, tightened all connections there was loose connection on one side, that could of been the problem, we would check system during the 6 month inspection
Performed Walkthrough of jobsite to size and measure location for upcoming installation. Completed Wells Fargo Financing paperwork with Homeowners while onsite.
No hat, no 24 volts, noticed 5 amp fuse blown, open, check outdoor high pressure switch wire, made repairs and test unit ok, cycle heat pump. ok,
Performed oil heat tune up, check electrical low and high ok clean exchanger and flue pipe, replace oil rf-1 and .60x70B nozzle clean and adjust electrodes ok flame detector ok check oil flow and pressure ok smoke test ok combustion test cycle furnace ok check draft ok also service humidifier new pad test ok set to winter 35%