Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Luis does great work and we are always very pleased.
Luis always does a great job, is on time and is always very helpful.
Five years ago, I never heard of this company, my heater died on the coldest day of the year and I called everyone that I had seen advertised on TV and no one would come out. Someone gave me this name and they were here in a heartbeat. Same thing happened with my AC going out on the hottest day this year, and guess who was here in a minute. Really, when you're freezing or too hot to even think and your system has a problem, there is nothing more important than knowing someone will be here to help. That is this company!
Luis was great. Thanks for sending him
Service Technician was on time, very nice, professional and completed work required. Very pleased.
Pleased with technicians work and he is a nice guy
Service was great, on time and Luis is very helpful and professional.👍
Knew what he was doing and had a lot of great info to share.
Installation of hard start assist and adding ac renew check operation of ac unit ok inrush amp draw 15 amps cycle ac unit ok
Performed ac tune up, found ac unit not working upon arrival, condenser fan motor not running, check electrical low and high voltage, canâ€™t flushed drain not an opening to clean drain, check blower motor and cap, check outdoor unit found open fan capacitor, tried new cap for testing, found condenser motor getting hot more than normal, also unit is running low on refrigerant, refrigerant is no longer available, due to required repairs would recommend replacement of system, also found pressure relief valve from water heater leaking, water heater heater is from 2012. We could replace pressure relief valve or water heater replacement. Called Mary to let her know the situation but did not answer. System is from 2003 would highly recommend system upgrade.
Performed ac tune up, check electrical low and high voltage connections, flushed drain currently does not have ez trap, test pump ok check airflows, check filter ok, found some dirt/dust on blower wheel, check outdoor unit refrigerant pressures capacitor and contactor ok noticed compressor starts on high amps, would recommend adding hard start kit and adding ac renew. Cycle system ok. Customer is interested on compressor recommendations, office will get back to customer.
Performed precision a/c tune up on American standard a/c system. ( homeowner to replace dirty filter) odd size ( 2) filters put together to make 30x30x1. Found no surge protection on ecm blower motor, installed ecm surge protector. Checked temperature split at indoor unit. Blew out condensate drain. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. A/c system is working fine at time of service.
Performed Quality Assurance on Bosch Heat Pump system. Reviewed installation with homeowner and answered any questions that he had. Completed checklist form in system. Ran system in heating mode and tested Temperature splits. Filled condensation pump to test operation. Tested EZ Trap Safety. This install passed the QA Inspection. No follow up needed. Collected check for remaining balance of installation.
Installed new Bosch air handler and outdoor unit. Installed new outdoor unit on crushed stone and leveled pad. Installed new disconnect, whip and surge protector. Installed new lineset in drop ceiling. Pressure test system past 300 psi and evacuated below 500 microns. Installed new air handler on new 12in return box. Installed new Aprilaire 2410. Installed new return drop and transition with cloth connector. Installed new supply plenum with cloth connector. Sealed all duct connections. Installed new ez trap and condensate pump. Installed new vinyl tubing to indoor discharge. Made all necessary high voltage and low voltage connections. Tested system in heating and cooling, system working properly.
No heat, found furnace turned off, turned switch off and increase temperature on thermostat check operation of furnace cycle couple times did not see any issues every time furnace went trough trial for ignition, based kn why customer says gas valve clicks but wonâ€™t ignite burners, during todayâ€™s visit burner ignite every time there was call for heat, furnace is a spark ignition system, if problem happens again we can replace electronic ignition module to tried to solve issue, furnace is from 2001 would recommend replacement of HVAC also provided an estimate to come back and replace ignition module, customer is aware that other electrical components might have to get replaced. Customer will office for repairs or system replacement option
Installation of hot water heater, removed old tank and installed new Bradford white water heater storage tank, adapted water piping as needed installed new expansion tank, two new shutoff valves one in hot and one on cold side, check for water and gas leaks, no leaks present, check water pressure reading 75 psi, there is no pressure reducing valve in the house, purge all faucets and put water heater on operation set thermostat to hot and went over with customer on their new water heater.
Supply air high stage 112/73 low stage 115/73 Performed 6 month inspection on recently installed furnace check all electrical components and connections, replaced filter, check burners cleaned sensor and check gas pressures performed combustion test check airflow temperature and settings delta is within manufacture specifications
Performed propane gas furnace check up, check electrical low and high voltage connections, replaced filter, cleaned sensor and check burners/ignition, check manifold propane pressure ok performed combustion test check supply and return air temperature, and static pressure, static on rerun is .65 wc, currently has a 16 in flex, we could add return box and add a 12 in flex to main rerun trunk to get more air circulation on furnace, also would recommend replacement of igniter and flame sensor, too much Corrosion around ceramics, called Henry and informed him about todayâ€™s visit, he will wait on recommendations for now.
Customer is concerned that the heat pump is constantly running, upon arrival found thermostat set point o be 69 room temperature is 69. Check heat pump operation pressure air flows ok, supply air 88 return air 65 check refrigerant pressures ok, once back up heat came on supply air was 108, found no issues with heat pump, heat pump is working within manufacture specifications, no charge for todayâ€™s visit.
Installation of 50 gallon electric water heater
Electric water heater not working, customer has hot water water heater is leaking and need to be replaced, quoted for new water heater 50 gallon electric customer approved replacement. We will be coming back tomorrow to install new water heater
Performed heat pump check up, check electrical low and high voltage connections, replaced filter check back up heat and regular heat, supply and rerun air temps ok. Check outdoor unit refrigerant pressures capacitor and contactor ok test defrost ok heat pump is working normal numbers.
Performed oil cleaning tune up, check electrical low and high voltage, cleaned heat exchanger and flue pipe, replaced oil filter, nozzle and pump strainer, check oil flow, replaced electrodes, AF11 HLX HEAD cleaned cad cell, per combustion test check airflow and static pressure ok, cycle furnace ok. Air filter was change last week, customer will take care of humidifier. Informed customer about burner transformer burnt lead, part is working if customer has issues with transformer parts will need to be replaced, AF11 transformer, provided an estimate for replacement