Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip and Amana condenser. Flushed lineset. Brazed in lineset with nitrogen. Installed new drip pan and unico high velocity system. Wired in control module and attached the 2 halves. Connected supply and insulated. Installed new ez trap and wet switch and wired to break r. Reattached condensate drain. Brazed in lineset with nitrogen and pressure tested to 300 psi then evacuated down to 167 microns. Wired in electric strip heater and tested. Tested in cooling and adjusted charge. System working great at time of install.