Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Package air-conditioning unit now working found thermostat off upon arrival instructed customer to set thermostat to call for air-conditioning 65 checked AC operation found condenser fan motor not spinning check capacitor capacitor is within range noticed blade is very hard to turn...unit needs a new motor and blade. Blade would not come off the existing motor quote for repairs would recommended having home comfort consultant to come out and provide an estimate on replacement