Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Quality Assurance On recently installed Indoor Coil and Condenser. Filled out attached Checklist. Reviewed installation with Homeowner.
Installed new coil and outdoor unit ran all new linesets and thermostat wire and drain. New whip disconnect was cut out in siding so we kept old one. Checked pressures and weighed in 1 pound ran 44 ft of line set had to charge for 28 ft. System was checked in ac and ran great. Delta t 26 degrees
Performed two ac tune ups, check electrical low and high ok flushed drain test pumps ok replace filters, blower cap ok, outdoor capacitors and contactors ok first floor system ok second floor unit is low on refrigerant pressure system with nitrogen and found outdoor coil leaking, recommended replacing system, heater and ac unit to match system, Office to set up visit