Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Checked no cooling complaint, found condensate pump full and safety tripped. Blew out discharge line, found no restrictions. Tested pump again, pump has failed. Replaced condensate pump. Tested pump. Started air conditioner, checked refrigerant charge, found low on charge. Topped off refrigerant charge, balanced by superheat. Checked operation and temperature drop across coil. Signed up first floor system for maintenance plan need to schedule cooling ptu.