Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed heating maintenance, replaced air filter. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap and drain. Serviced humidifier, cleaned and replaced water panel. Started humidifier, checked operation and set humidistat to 35%. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
We over System with bob and after tracing everything found that the next step is to located the zone valve for the nursery area to see if it is operating correctly. Also old computer system that runs the entire system may not be programmed correctly, bob will try to locate the zone valve and test it to see if it needs replaced.
Performed heating maintenance, found condensate pump has a broken discharge housing where the fitting connected to. Replaced condensate pump, tested pump. Cleaned burner and flame sensor. Inspected heat exchanger. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Started boiler, checked boiler pressures and temperature. Tested limit and safety switches. Performed combustion test.
Performed heating maintenance, cleaned ignitor and flame sensor. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections. Cycled circulators started boiler, tested limit and safety switches, measured fuel pressures. Performed combustion test. Checked boiler pressure and temperature. Need to set up an appointment for a ductless mini split for the basement.
Relative Humidity exceeds 55% during demanding days. even with AprilAire Whole home dehumidifier. Monitored Relative Humidity/Indoor return wet bulb throught my time at the house. %RH did not exceed 52%. Wire R, C, and G from equipment to DEHUM control, following install manual. ( Prevents outlet air from entering inlet of dehumidifier). Will make comfort consultation appointment with Joe to attempt to give a definitive solution to humidity problem. (Second attic AC system or another Whole home dehumidifier).
Return visit to perform combustion test on boilers 2 and 3, check gas pressure incoming and manifold pressure, incoming is 5.8 wc burner canâ€™t be adjusted at this time firing rate should be equivalent to 4 inches water column, customer need to contact peco to increase gas pressure so we can get 4 inches water column on manifold side to archive the 200 k btu firing rate there will be an extra charge for next visit
Performed cooling maintenance, checked air filter ok. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil
Checked no cooling complaint, set thermostat to cooling, started air conditioner, checked air filter, blew out condensate trap. Checked refrigerant charge ok. Checked run capacitor. Found a failed hard start kit. Replaced start kit. Cycled air conditioner. Checked operation and temperature drop across coil.
No cooling 3.5 Ton Trane AC system. High head pressures high subcooling. Found noticeable leaks on ubends of indoor coil. By the time homeowner had shut windows TD was 20F. 21 superheat; 14 subcooling 239/67. Problems are caused by a combination of leaking indoor coil and failed)clogged piston. Advised homeowner to use less restrictive filter and keep windows shut.
This proposal is to provide a maintenance agreement for the 3 gas boilers in the basement and includes annual maintenance. It also addresses the leaking relief valve replacement, 4-9-2021 cleaned all three boilers, cleaned heat exchanger and flue pipe, boilers were super dirty, removed all debris, check electrical connections and check gas pressure, performed combustion test check water pressure and temp ok when doing a combustion test found two boiler running on high co, check chimney draft, air intake manifold gas pressure, gas pressures as set at 1.87wc could not adjust gas up to 3.5wc incoming gas pressure to building is 5 inches wc would recommend contacting peco to increase gas pressure also during visit replaced relief valve for boiler 2 middle boiler, check for leaks no leaks found, return visit required to check combustion on other two boiler, not sure if combustion Analyzer is working properly
Customer has three boilers commercial set up, customer has to add water once a week, check water pressure and reading 20 psi, customer has questions, I currently donâ€™t have the answers I will have if Iâ€™ve get back to customer
Performed Precision Heating Tune Up on Weil McLain High Efficiency Boiler. Cleaned Heat Exchanger and Flame Ignitor assembly. Cleaned Condensation Pump and tested. Found pump was not pumping the proper amount of water out. Found the Check Valve on the Discharge had gone bad and was not opening properly. Replaced Check Valve and filled pump multiple times to test operation. Put system in operation and measured Combustion Readings. Found water pressure to be higher than normal at around 30 PSI. Removed Water from boiler to lower pressure down to around 20 PSI. Checked Expansion Tank and checked Water Feeder. Also found unit was intermittently going out into a lockout and then reset itself due to the Supply Water Temperature sensor. Found a loose connection at the wiring terminal for the supply water sensor. Reconnected wiring and tested. The gaskets are starting to become worn on the system. Would recommend on next tune up having all of the Gaskets replaced using the Weil McLain mainte
Checked no heat complaint, found thermostat blank, itâ€™s a 2 wire thermostat, checked batteries ok. Found corrosion on the thermostat battery contacts. Cleaned thermostat contacts. Installed batteries. Checked voltage ok now. Installed thermostat. Cycled boiler and checked operation.
Performed heating maintenance on gas boiler, cleaned burner and ignitor. Blew out condensate trap. Checked for errors. Checked voltage, amperage and electrical connections. Started boiler, tested limit and safety switches. Measured fuel pressures. Performed combustion test. Checked boiler pressures and temperature.
Here in Spring City checking the refrigerant charge as part of an AC Tune-Up on a Bryant system. The Condenser is sitting on the roof with the furnace in a closet below it.