Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Customer complain is that bedroom is hotter and colder than other parts of the house, check airflow and temp coming out of vent,,good volume come out at 50 degree, room is 13x14, ductwork is not exposed, booster fan would not help in this situation, could be noise and will be uncomfortable, would recommend setting fan to ON all the time This will could bring more comfort inside the room would even out the temp from rest of the house, is this seems to help new thermostat with room sensor should be installed could be installed, this would take the average of the room and rest of the house, customer wants to installed t10 with sensor and also performed heat tune up,
No heat found unit off on pressure switch code, reset unit and test operation unit would run for minute or two then shuts off on pressure switch, check vacuum and venting ok, inducer had some water, exhaust drain port had some blockage, cleared drain port behind inducer and check in line vacuum negative pressure and is over rated pressure switch, one side is -.70 and condensate port is -1.45 one switch is rated at -.35 and other is rated at -.75 wc. After cycling furnace couple times run heater for 20 mins and performed combustion test, noticed intake and exhaust termination is under a deck informed customer and recommended extending intake all the way to the outside of deck
Performed precision heat tune up on icp propane gas furnace. 20x25x1 air filter is clean. Blew out condensate drain. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Recommend surge protector for ecm blower motor. Gas furnace is working fine at time of service.
Performed ac check up check electrical low and high ok replace filter, flushed drain line, could not clean trap, seems to draining ok check split ok outdoor unit 410 pressures contactor and capacitor ok cycle unit ok
Performed gas heat inspection check electrical replace filter flushed drain, clean sensor gas pressures ok combustion test cycle heater ok show customer drain piping, trap is all the way at bottom can't clean trap recommended adding an ez trap and union for better cleaning Also two zones system first floor and second floor, 2nd ok, first floor has two dampers in series combustion controlled by first floor stat, one is stock closed manually open and disconnect damper per customer, to make repairrs 14 in withd by 8 in height ,,, new damper has to be 14x8 with motor damper on the 14 in side
AC Tune Up - changed filter . Tested and cleaned condensate Pump. Tested Capacitors. Tested air temperature splits and refrigerant charge. Tested overall system and system is running to factory standards. Heat Tune Up . Tested combustion. Cleaned vacuum switches . Cleaned flame sensor. Checked humidifier. Tested air temperature splits. Tested overall system and system is running to factory standards. Water heater . Homeowner states that waterheater shuts down while taking a shower . I tested the water heater and found a dirty flame sensor. I cleaned the flame sensor and recaulked with high temperature caulk to seal . Tested the water heater with the shower and kitchen faucet running . Water heater started up and ran fine . Tested overall operations and the waterheater . Water heater is running to factory standards .
Trick or Treating Tip #1 - Make sure someone in the group carries a flash light. This is helpful for doing inspections of the HVAC units at the houses you are collecting candy from after it gets dark outside.