Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed ac check up check electrical low and high ok replace filter, flushed drain line, could not clean trap, seems to draining ok check split ok outdoor unit 410 pressures contactor and capacitor ok cycle unit ok
Performed gas heat inspection check electrical replace filter flushed drain, clean sensor gas pressures ok combustion test cycle heater ok show customer drain piping, trap is all the way at bottom can't clean trap recommended adding an ez trap and union for better cleaning Also two zones system first floor and second floor, 2nd ok, first floor has two dampers in series combustion controlled by first floor stat, one is stock closed manually open and disconnect damper per customer, to make repairrs 14 in withd by 8 in height ,,, new damper has to be 14x8 with motor damper on the 14 in side
AC Tune Up - changed filter . Tested and cleaned condensate Pump. Tested Capacitors. Tested air temperature splits and refrigerant charge. Tested overall system and system is running to factory standards. Heat Tune Up . Tested combustion. Cleaned vacuum switches . Cleaned flame sensor. Checked humidifier. Tested air temperature splits. Tested overall system and system is running to factory standards. Water heater . Homeowner states that waterheater shuts down while taking a shower . I tested the water heater and found a dirty flame sensor. I cleaned the flame sensor and recaulked with high temperature caulk to seal . Tested the water heater with the shower and kitchen faucet running . Water heater started up and ran fine . Tested overall operations and the waterheater . Water heater is running to factory standards .
Trick or Treating Tip #1 - Make sure someone in the group carries a flash light. This is helpful for doing inspections of the HVAC units at the houses you are collecting candy from after it gets dark outside.