Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service call that there was a noise coming from the Furnace/Indoor Unit. Upon arrival found thermostat set to 74 in Cooling Mode and the Indoor Temperature was at 80 Degrees. The Blower Motor was not running and the Outdoor Unit was running. Found Blower Motor had seized and failed. Removed old Blower Motor and installed a new 115 V 1/2 HP 3 Speed Blower Motor. Made all wiring connections and installed a new 10 Mfd Blower Motor Capacitor. Put system back in operation to test. After running system, found the Refrigerant Charge was low. System was only producing about a 12 Degree Supply Versus Return Air Temperature Differential. Added 2lbs of R-22 to System, Charging by Superheat for a Piston. Refrigerant levels increased to normal levels and Air Temperature Differential Increased to 16 Degrees. System is in poor condition. Due to age and condition of system, would recommend replacement of the Gas Furnace AC System before any further issues occur.
Drained, disconnected, removed, and disposed of old water heater. Installed new 40 Gallon Natural Gas Atmospheric Water Heater in new aluminum pan and elevated with cork pads. Installed new Water Alarm. Completed mechanical and piping connections to water heater. Installed new vent Pipe and sealed to Chimney Base. Filled and purged air from water heater and tested operation.
No heat service call in Woodlyn. After troubleshooting the Ducane Gas Furnace, found the Control Board and Thermostat were not working properly and needed to be replaced. Installed a new Honeywell Thermostat and a new Honeywell Universal Control Board.