Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Customer concern- no heat Upon arrival found furnace locked out on excessive retries. Checked all pressure switches and found blocked drain switch to be faulty. Rated at -.10 inwc but opened and stuck open at 2.3 inwc. I jumped out switch so they would have heat. Will need to return to replace pressure switch. Office will follow up on Monday to schedule a date.