On arrival homeowner was concerned about water coming out from the emergency drain. I inspected the primary drain and discovered that the primary was backed up severely. I also discovered that the float switch gets triggered and shuts off the system at the hottest points of the day. I recommend to install a ball valve and to flush the drain line. I flushed the primary drain line and tested operations. The system is working properly at this time.