Very nice about explaining what had gone wrong and things to watch out for in the future. Was unable to do anything the first day because the lines were frozen (my fault) so he went out of his way to come back the next day to take care of the issue. Great value and thorough.
Alex and his crew were terrific! He provided me with a quote, and then he came over a couple days later and completed the job in a short time frame. Efficient service!
Service was awesome! Fast, polite and helpful. Knowledgeable, gave helpful tips about troubleshooting in the future. Would recommend them to friends.
Quick service and very courteous
Alex was incredibly professional, friendly, knowledgeable, and helpful. I could not have asked for a better HVAC experience (and I have had many due to a pesky furnace)! I will be recommending you guys to all of my friends!!!
Alex and E&M is the most responsive and fairly priced HVAC company I've ever worked with. Recently had AC go out he was there to troubleshoot the problem the same day. The very next morning he was there again with the replacement part. An housr later we were up and running again. All at a fair price. You can't ask for anything more.
He was right on time, through, and affordable
Response from E&M HVAC INC.:
Thank you Natalie! It was our pleasure. Hopefully you will use us in the future!
No coolingreplaceddual capacitor
Repair drain lines and clean ac unit
Replace condenser fan motor
Kriste nenanis ac installation
No cooling unit had loose schrader core
No cooling unit kept popping 3 amp fuse traced back to a bad contactor and also did tune up on ac unit
Erik install chimney liner
No heat found bad thermocouple replaced
No heat gas was shut off
New furnace installation
No heat bad hose on pressure switch
Furnace tune up