Knowledgeable, friendly and efficient.
Cameron is a nice kid he knows job very well don’t let him leave you guys 👍
Chris was polite, friendly, thorough, and happy to answer all of our questions! Everything was great, but there was a discrepancy with the price. I was told over the phone that it would be $95 & $85 for the two fireplaces, but we were charged $95 & $95.
After having another contractor out, and being told our boiler was out of warranty, and being quoted several thousand to replace, I called Evans for a second opinion. They came out promptly, and got us back up and running, and got us a new boiler under warranty! They were very polite and helpful, and I have been recommending them since. Thank you.!
Ruud furnace repair , install in Emerson T stat and perform a maintenance on the furnace . Furnace is operating good no issues at the time of testing . Gas line inside furnace was starting to rust . I cleaned it up and paint about 1 1/2 feet of black iron .
Checked furnace for signs of an issue due to noisy operation heard upon the first time the furnace was used this season. Everything is working well, no longer making any rattling noises. No cause for concern found at this time. Fireplace thermostat had come off the wall but was not broken, secured it to wall and tested operation. Working as it should, no issues.
Furnace maintenance and inspection. Increased cooling fan speed to high to help with warmer temperatures on second floor. July 11th: air conditioning maintenance. Unit was very loud on arrival. Outdoor unit contactor was failing. Replaced contactor under warranty. Unit quiet and running normally. Recommend maintenance again next year due to the location of the unit. It was very dirty.
Lennox furnace and ac maintenance
Furnace cracked heat exchanger, will get furnace with us. Fireplace maint, cleaned and painted inside. CX very happy. Only charged for fireplace maint
Furnace repair , Lennox furnace over heating , and possible having intermittent issue turning on ( customer suggested, he has been resetting the power to get the furnace to operate) tested the motor , and turned up the fan speed , T stat is also dropping 26 v to w , which is making the furnace cycle on and off , installed new Emerson programmable T stat
Maintenance and inspection of Carrier furnace and Lennox air conditioner.
Ac repair - system low in charge Found loose nut on txv - tighten and explain to customer that may have fixed it, but no gaurentees. He would like to be proactive and install a uv dye. Added 1 lb of 410a..System fully operational.. Furnace maintenance - system is fully operational. Motor is starting to make sounds on start up customer will monitor.
Service call. Repaired gas leak at flex connection on stove.
Complete humidifier installation.
Maintenance and inspection of fireplace.
Furnace and heat pump maintenance.
Power vented water heater installion