I was delighted to have Kyle service my furnace - he was so polite, informative and did an excellent job of analyzing and fixing my furnace. As a representative of the company, you couldn't ask for a better person - I would welcome Kyle into my home any day. Thank you
We called Evans Heating & Cooling to service our fireplace and they were able to come within 24 hours. The service technician explained everything he was doing in detail, cleaned the fireplace, painted the fireplace, rearranged the logs to be more aesthetically pleasing, and added some embers. The fee was well worth it, and above everything else he was so friendly. Highly recommend!!
Chris did a great job. Knowledgeable technician
Friendly professional service
The service we received from Evans Heating and Cooling was outstanding. Both the Office staff Ladies were most helpful and understanding. The service technician came on time and did a thorough examination of our faulty furnace. The diagnosis was accurate, the required replacement pressure switch ordered and expedited. It was replaced today and furnace now working 100% An excellent company to deal with. I highly recommend them.
We had Chris last year for the furnace and fireplace maintenance and we requested Chris again this year. His very nice, polite and knowledgeable 👍🏻👍🏻👍🏻
Very nice gentleman.
Great. Polite, on time, neat, and informative. My go to place for heating!
great service, great attitude, very thorough, pleasant,i have not had this quality of service in many years.thank you.
I would definitely recommend Jordan as he is efficient, quick and honest! Neighbours, family and friends will know how great Evans Heating and Air conditioning company really is!!
Fireplace maintenance and inspection
Furnace maintenance. Furnace was very loud. Vent had negative slope from installation. Condensation water had no where to drain. Venter motor was struggling to keep up with all the water in motor. Removed motor, drained the water, corrected venting. Furnace nice and quiet.
17 gal Humidifier install and tankless maintenance Fixed loose exhaust clamp..see photos
Goodman furnace maintenance and Hrv and quote for new humidifier
Luxaire furnace maintenance
Lennox furnace repair after hours , spider nest in channels to pressure switch on the back of collector box , removed collector box and cleaned out with compressed air
Furnace and fireplace maintenance
Lennox furnace maintenance, cracked trap , sealed with caulking , furnace in good condition
Coleman furnace repair , replaced dual pressure switch
Goodman furnace maintenance, and service call on hepa filter , customer woukd like to quote to replace part in hepa filter
Ameristar furnace maintenance , furnace was installed in 2020 on a foam pad
Lennox furnace repair / maintenance, condensation trap cracked ( sealed with caulking ) inducer motor starting to vibrant and make a small amount of noise , no other noise heard while testing , furnace was over heating I have change heating tabs from yellow to black to allow more air flow , ac evaporator coil is clean, furnace is still cycling off on high temp , blower motor amps are good , wheel is fairly clean , motor could be failing , customer only have two returns up stairs , I have recommended to possibly add one more return down stairs