Great service! Quick response!!
Technician arrived on schedule, took precaution to cover his shoes and proceeded to repair our gas log. Overall we were quite pleased with everything and will use your firm again if the need arises.
Josh Walker was great! Very thorough and informative in sharing what he found and what my options were. I will remember and recommend him and Excel Comfort Services in the future. Your company's responsiveness and quality service is better than the slick TV commercials I frequently see other companies show on TV.
Made sure everything is in working order
Very nice and answered any questions. Instilled trust and will recommend.
They arrived when they said they would and quickly diagnosed and fixed our fireplace.
Excellent service by Josh. Extremely professional and ensured all of my questions were answered. Fixed the problem to include finding and fixing a small gas leak.
Gas fireplace service no repair needed
Plumber needed for Toilet repair near Danforth rd
Ac repair near waterloo rd capacitor replaced
Ac repair near me
Ac repair Faulty run capacitor
Carrier ac repairs needed Low refrigerant
Ac repair low refrigerant near mercy hospital
No gas water heater repair near covel rd
Ac repair near Edmond ok
Finding north ac system not working ac repairs needed on run capacitor voltage enhancement system and also finding that system is low on refrigerant 22 replacing run capacitor and installing performance enhancement hard start kit upgrade and installing freon due to low refrigerant on system with 76 degrees superheat
2007 bradford white 50 gallon gas water heater needs replaced due to repair not feasible water heater installation occurring in or around 2007 when water heater manufactured
Finding faulty 50/7.5 mfd run capacitor for ac repairs near waterloo Rd hvac installation occurred approximately 15 to 20 years can't read nameplate of goodman condenser
35/5 run capacitor faulty in ac repairing voltage enchantment system for ac repairs near Douglas rd 248 volts ac load side .75 amps rla condenser fan motor 11.3 amperage rla compressor motor York condensing Unit installation over 20 year old but still running strong
R22 Lennox straight ac Condensing unit restricted heat transfer media coil Cleaned and washed ac coil and refrigerant pressures are much better 83 psi suction side 16 degrees superheat 252 psi high side pressure 17 degrees subcooling Repairing ac unit now for homeowner Installed hard start kit to system
2 ton American standard ac Condenser repair service call appointment Faulty compressor short to ground in start winding and no continuity between any windings. Needs me compressor replaced or new heating and air conditioning unit installation done.