Great service! Quick response!!
Technician arrived on schedule, took precaution to cover his shoes and proceeded to repair our gas log. Overall we were quite pleased with everything and will use your firm again if the need arises.
Josh Walker was great! Very thorough and informative in sharing what he found and what my options were. I will remember and recommend him and Excel Comfort Services in the future. Your company's responsiveness and quality service is better than the slick TV commercials I frequently see other companies show on TV.
Made sure everything is in working order
Very nice and answered any questions. Instilled trust and will recommend.
They arrived when they said they would and quickly diagnosed and fixed our fireplace.
Excellent service by Josh. Extremely professional and ensured all of my questions were answered. Fixed the problem to include finding and fixing a small gas leak.
Very courteous and professional.
No gas water heater repair near covel rd
Ac repair near Edmond ok
Finding north ac system not working ac repairs needed on run capacitor voltage enhancement system and also finding that system is low on refrigerant 22 replacing run capacitor and installing performance enhancement hard start kit upgrade and installing freon due to low refrigerant on system with 76 degrees superheat
2007 bradford white 50 gallon gas water heater needs replaced due to repair not feasible water heater installation occurring in or around 2007 when water heater manufactured
Finding faulty 50/7.5 mfd run capacitor for ac repairs near waterloo Rd hvac installation occurred approximately 15 to 20 years can't read nameplate of goodman condenser
35/5 run capacitor faulty in ac repairing voltage enchantment system for ac repairs near Douglas rd 248 volts ac load side .75 amps rla condenser fan motor 11.3 amperage rla compressor motor York condensing Unit installation over 20 year old but still running strong
R22 Lennox straight ac Condensing unit restricted heat transfer media coil Cleaned and washed ac coil and refrigerant pressures are much better 83 psi suction side 16 degrees superheat 252 psi high side pressure 17 degrees subcooling Repairing ac unit now for homeowner Installed hard start kit to system
2 ton American standard ac Condenser repair service call appointment Faulty compressor short to ground in start winding and no continuity between any windings. Needs me compressor replaced or new heating and air conditioning unit installation done.
53.8/7.43 microfarad reading at run capacitor rated @ 55/7.5 mfd 440vac R22 system piston metering device Lennox heat pump condensing unit installed 2009 218 psi high side 8 degree subcooling 83 psi suction side 25 degree superheat 12.5 rla compressor 1.7 rla condenser fan motor No ac repair needed near air conditioner system
R22 condensing unit low on refrigerant r22 freon has large leak while running only has 15.6 psi low side pressure and 170.9 psi high side press. System is either a 2000 model or a 2004 according to serial # Needs ac repair low freon puron r22 r410a near waterloo rd
ruud ac Condenser tune up service R22 refrigerant piston metering device Low side 63psi 32 degree superheat 33 degree saturation vapor temp High side 291 psi 28.5 degrees subcooling 127 degree saturation bubble liquid temp 14.9 rla amperage compressor motor 48.5/3.04 microfarad run capacitor rated at 50/3 mfd 440 vac titan HD capacitor 1 amps rla od fan motor 240 volts ac Low on refrigerant 22 freon low repair needed adding freon refrigerant and calibrating superheat adding leak sealant vapco
Ac repair for Lennox air conditioner repairs and renovations due to faulty capacitor and contactor relay switch 24v coil replaced and installed with new systems
Downstairs ac Condenser trane repairs not needed 1.2 rla condenser fan 13.3 rla compressor 246 volts ac R410a refrigerant txv 123 psi suction 16.8 degrees subcooling 42 degree vapor saturation temp 322 psi high side pressure 11.7 subcooling 101.5 bubble saturation temp 59.7 mfd / 4.97 mfd capacitor rated at 60/5 mfd 440 vac
Trane clean effects cable power control 2x3 plug with thermostat cab01157
2 ton condenser installed around 2010 245 volts ac 5.7 amps rla compressor .7 amps outdoor condenser fan motor R410a refrigerant txv valve metering device 117 psi 21 superheat 309 psi high side 11 subcooling