We have used this company since it opened several years ago. They are TOPS. I would not even think of using anyone else. They come to fix your problem within hours of your call, not days, but hours. And they are the kindest. I had a furnace issue this morning, called about 930am, they came at 1030am and fixed my problem. Now if I can get my feet thawed out, I will be fine.
Technician was great very patient he get the job done
Well the worker was very professional, friendly, and on time, started the job, didn't stop until it was completed, explain how the unit work, and if there was a problem just call them.
Took less than 30 minutes very nice very knowledgeable
Guys were professional
Very professional and provided excellent customer care
On time very polite
Unit not operating in heat. Found t-stat with settings not correct.
Installed a new Carrier mini split for customers new man cave addition in Valley Alabama.
Unit not cooling found disconnect burned up. Replaced disconnect.
Package unit not heating. Found breaker tripped. Reset breaker and tested system. Breaker tripped. Found the breaker to be bad. With disconnect outside off the breaker would not reset and would trip. Replaced breaker and system runs as it should.
Thank you to the Jones family for trusting the team at Express Heating and Air Conditioning to take care of their home comfort needs!! Our best crew is here installing a new energy-efficient cooling system! 706-576-6800 call us today to schedule your AC upgrade.
New heating and air conditioning system estimate in Columbus, GA. Call Express Heating and Air Conditioning for your estimate, 706-576-6800.
Replaced leaking Evaporator coil on a carrier split system. Replaced coil with pen parts. Replaced the bad condenser fan motor and dryer on unit as well. Pulled vacuum on the system. Charged system accordingly and tested system operation. System is running as it should for our military customers in Fort Mitchell, Al.
Replaced a bad outdoor fan motor on the walk in cooler at MK Mart in Columbus Columbus, GA. Also gave an estimate to replace the outdated 1970s model. Call Express Heating and Air Conditioning for all your cooling needs, 706-576-6800.
Replace an out of balance blower wheel and a 25 year old Goodman furnace.
10 year old system with a major leak. Added refrigerant and performed leak search.
System not running. Off on drain safety. Cleared drains and tested system.
Ductwork and insulation replacement estimate in Columbus, GA. Call Express Heating and Air Conditioning for all your home comfort needs, 706-576-6800.
No cooling on a 2 story house with 1 zone. Outside unit not running. Refrigerant is low causing unit not to run.
R22 system not cooling. Found system very low and informed homeowners of findings. Recommend new system.