Performed furnace tuneup, this is first visit on new contract. Bearings starting to make noise on inducer- amp draws are under max rating. Homeowner was doing floor remodel and cracked tee for condensate line. Unable to replace just the tee due to space constraints, Replaced starter, portion of pvc and cracked tee. System is operating properly at this time.