Performed ac tuneup. Found condensate pump motor failed. Replaced condensate pump and added reservoir treatment. Verified proper operation of condensate pump. Ac is 20 yrs old, amp draws are within range, high side pressures are out of range and compressor failed megohmeter test indicating compressor insulation is compromised. Recommend proactively getting replacement quote before system completely fails.