Really enjoyed coordinating the HVAC appt, the synopsis of our unit, the repairs, and the ease of scheduling an appointment.
Tyler was a very nice/polite man who explained things well enough to completely understand. He made calls to see if I'm under warranty so I can save some money. Looking forward to him coming out next week to finish the job.
Could not get system to duplicate loud sound. Judging by the video shown, sound like compressor was having a hard time starting. Found 60/7.5 start assist reading 54.3/7.53. Replaced 60/7.5 start assist. All readings are within manufacture specs and system is operating correctly at this time. There is a slight vibrating noise at condenser. Fan motor and compressor amps are within manufacture specs, vibration could be grid surrounding condenser coil. System replacement is recommended due to age (2008) and phase out of R22 refrigerant.
Ac service call in McCordsville Indiana.
Performed spring tuneup. This is last visit on current contract, will need to renew for winter cleaning. System is operating properly at this time. Addressed customer concern with upstairs bedroom getting hot in early am. No scheduling is set to change after sleep period starts. Heat is set to engage when temperature drops below 70°. Removed scheduling per homeowner
Maintenance in mccordsville
Second opinion call in mccordsville Indiana.
Second opinion call in McCordsville Indiana
Ac tune ups in McCordsville Indiana.
Ac tune up in McCordsville Indiana
Residential hvac installation
Repairing an AC unit in McCordsville
Yearly maintenance on a heat pump in McCordsville