Performed heating tuneup, this is last visit on current agreement. System is functioning properly at this time, recommend checking filter in a month. Passed carbon monoxide test at 0ppm. Addressed condensation issue after evaporator coil replacement. Coil is sitting on insulated riser box and ductboard that is wrapping supply duct is deteriorated at bottom foot. Will rewrap that portion on spring tuneup.
Pull furnace to install new 4ton American Standard coil
Upon arrival evaporator was frozen solid. Verified airflow was correct, filter was good. Turned on heat to thaw out. Found system low on charge, performed leak search and found hits at evaporator coil. Scheduled install team to come out 7/19 to pull furnace and install 4ton coil. Charged system up to proper specs in the meantime.
Pendleton - new furnace & ac, all new duct work/ thermostat