Very professional, great service and knowledgeable.
Clean & Check service Tested AC system. Inspected inside and outside units. Furnace has dirty blades and coil. AC compressor is loud and has high pressures.
Performed ac tuneup both front of house and back of house units. Filters were incredibly dirty on both units, changed all 4 filters and verified proper operation of both units at this time.
Blower wheel is pulling 14 amps on startup. Wheel is pretty dirty. Motor is going out. Evaporator coil is getting close to freezing that could be because the blower isn’t moving adequate air or it could be low on refrigerant. Outdoor capacitor is also bad. Matt is going to come out to give options.
All major components are working well. Filter is not catching all debris. Blower wheel is getting dirty. This is going to make unit run more, at a low efficiency and shorten life expectancy. 1/8 of an inch of dirt on blower wheel can reduce efficiency up to 20%
AC yearly maintenance in Westfield.
AC yearly maintenance in Westfield
Ductwork replacement in Westfield
Maintenance in Westfield
A/c pm Indianapolis
AC Preventative maintenance service in Noblesville
Service call in Westfield
AC start up in Westfield Indiana