Installed first co air handler with Amana condenser, installed volume damper in master bedroom trunk duct, new lineset, secondary emergency drain pan, relocated thermostat to hallway, reconnected existing heating pipes and condensate pipe.
Checked operation of second floor system. Found system to be low on refrigerant. Dual capacitor tested out of range. Attic air handler biological growth on coil, and blower. Customer would like estimate to replace two floor system. Need to set appointment for replacement estimate.
Flush lineset and install 13 SEER Amana ASX1336, NO Merv filter,
Customer looking for an estimate for ac replacement.