Scott was punctual and worked diligently to figure out the issue.
Great service, as usual!!
Chris went above and beyond to service our AC. Highly recommend Folkes for all your AC Heating and plumbing needs.
Service was prompt and high quality. Service man was knowledgeable and courteous
Great service very professional
Noah was very helpful in helping us resolve a ventilation issue in obtaining a CO. He contacted fellow technicians in verifying his appraisal.
Customer stated they heard a mechanical noise for a split second when kicked on. Tested system 3 times with customer next to me to pin point noise he was hearing. Customer was hearing compressor kick on, informed customer that the noise is normal and the system is operating normally.
Arrived at customers house to install customer supplied sump pump. Removed existing pump and added 1.5 no hub coupling. Installed new pump and tested. Customer has a lot of ground water. Pump will run a lot.
Arrived at customers house for backup in shower in basement. After evaluating gave customer estimate on new toilet. She has multiple jobs she would to do. Customer would like to start with a new toilet and then get contractor over to give her estimate on new bathroom. Also went over duct cleaning as she would will schedule after toilet is installed so she does get confused.
Found drain line clogged, cleared line and water from coil pan drained to condensate pump, pump removed water. System operating normally.
arrived at customers to install customer supplied kitchen faucet. Found nut on drain cracked which was replaced. Also found the kitchen sink had a slow drain. After evaluating downstairs found that there is galvanized drain lines which are causing the slow drains. Gave customer estimate to replace galvanized.
AC tune up with MA. Would like a plumbing inspection having a issue with toilet in hallway. Please follow up Monday.
Called out for a clogged sewer. After speaking with the customer regarding the sewer clog I gave an estimate to snake the line. I removed the second floor toilet and snake 75â€™ into the main sewer. There was an excessive amount of tree roots in the line and I removed most. An estimate for the high pressure water jet was left with the customer. There is no sign of a back up at this time. Other work will be done during the week.
Replaced float switch and tested system.
Performed ac tuneup, checked all components. System is operating properly.
Upon arrival no power at thermostat or unit, breaker was fine, noticed emergency switch was off by laundry room, turned switch on and power to unit and thermostat. Tested system and everything came on. While I was here also performed AC tune up on one system. Changed return filter 16x25x1, tested capacitor which was in range, blower wheel amp readings were normal, had a 17 degree difference from Delta T. At condenser checked pressures which were normal, capacitor tested in range, contactor in good condition no burn marks on contacts. System operational and working.
Found all even room numbers second floor locked out on U9 fault. Spoke to manufacturer tech support, case #1625121. Performed reset on both PCB boards and checked system operation. Did find low temperature differential in rooms. Charged system with 6lbs of 410a and rechecked temperatures. 20 degree differential.
Replaced low MF capacitor, also replaced condenser fan motor, motor pulling high amp draw, tested, system operational.
Wants to get heating/AC in basement. THey are going to finish the basement and want to know pricing. Think they have ductowkr in this area also may be interested in a ductless unit whichever is more cost effective. Does not want solicitations on this estimate. Single family home. Gas for heat. Currently has central air.
Called out for a water quality test. After speaking with the customer regarding the water quality test I tested the water in the kitchen sink faucet for hardness, ph balance and iron. The results are 25 gph, ph 7.6 and iron is a .2. An estimate for a water softener was left for the customer and she will call when ready to move forward with the estimate.
Front bedroom over garage not getting heated or cooled properly. Has been continuous problem. Poor airflow to three supply on 10â€ trunk to opposite attic area from where equipment is. Ductwork was never sized properly and bedroom over garage also has large sliding glass door. Recommended ductless heat pump to properly heat and cool room. Need to set appointment for estimate.