We can not begin to express how satisfied we were with the exemplary service and professionalism. David went above and beyond in addition to giving us options. He took the time to assess our HVAC system and carefully listened to our concerns. We will never go back to Jones.
Performed annual AC tuneup on 4 systems. Cleared drains, checked wiring, duct work, capacitors, amp draws, pressures on all 4 systems. Tested units. Systems operational. Installed UV light on Master bedroom unit.
First floor not getting cool, air handler running condenser fan motor running but compressor was not running, checked pressures and system completely empty of R22 refrigerant, tested other two units for second floor and garage which those presssures were fine, customer is going to need a estimate for residential replacement for at least first floor. Has AC on second floor and garage.