Tony was great- very knowledgeable and steered us in a good way.
Danny is always professional, courteous and knowledgeable. Great experience!
Opened system. Found mice and bees have done extensive damage to outdoor system. Chewed wires, burnt board, damage to compressor and condenser cover. Need to set appointment for replacement estimate.
System low on r-22, recommend residential replacement, customer declined repairs due to she receiving estimate on Tuesday for price on residential replacement.
Finish installation, first company system with 18seer Amana condenser. Antifreeze may need to be added to boiler due to leaking heating pipes in the attic. Homeowner will call Bill for payment.
Compressor starting to fail for above garage system, also found capacitor low on MF, replaced, tested, system operational, recommend residential replacement. Schedule appointment for residential replacement
Condenser had bad capacitor, replaced, tested, checked pressureâ€™s, system operational.
Found outdoor ductless condenser not energizing. Indoor unit flashing error code. Operation light off and timer flashing two times. While opening outdoor system found there to be very large bees nest. Will need to be removed. Also tried call manufacturer. Keep getting no answer. May be closed for holiday. Will need to follow with with Fujitsu when open. And customer will have bees nest removed.
Found the drain clogged at the inside of the pan, cleaned it out and tested, unit drained and condensate pump removed the water. System is operating properly.
Completed annual maintenance on 4 ac systems. Performed leak search on basement ac. Found leak in evap coil. Customer would like estimate on coil replacement and estimate on replacement of system. Installed 4 Uv lights. Found condensate pump not operating on basement unit. Overflowing. Replaced condensate pump. Replaced all filters customer supplied
Found first floor system to be low on charge. Second floor system found compressor to be seized. Found all refrigerant and compressor oil has leaked out of system causing seized compressor. Recharged second floor system. First floor system needs replacement. Need to set appointment for replacement estimate.
Water heater pilot out upon arrival and would light after reset. The control module was flashing internal error code for control module. Replaced control module tested system through a few cycles and did fire every time and stay running. Water may take a little to heat up but was starting to get heat from sink faucet. Customer was without hot water for a few days.
System low on Freon, recommend residential replacement. Do not have access to refrigeration lines for repairs, lines are in walls.
Installed mini split 9k btu wall mount, evacuated and charged system to manufacturers spec
Completed annual maintenance on three ac systems. Found second floor system low on charge. Customer opted to have system recharged. Also replaced run capacitor for kitchen condenser.
Performed ac tune up, checked all components. Took standing pressures due to weather outside, charge looks good it is only 2 years old. Changed the filters and washed the condenser coil. All components are looking good at this time.