Very professional and thorough. Highly recommend
Unit not getting any power from thermostat, customer had insulation separated in attic from her contractor and found emergency float switch pinched under insulation, resecured float switch to emergency pan and unit came right on, no error codes at air handler or thermostat, let system run for 20 minutes and took delta t reading which was at 30 degrees, also changed return filter that was plugged from construction in home 14x14x1. Customer was not home only contractor will need to bill customer.
Recover the refrigerant from the system and take the 1 indoor unit off the wall until the demolition is done. After removing the one system tested operation of the other 3 units.
The customer would like one indoor unit on a room removed off the wall for a period of time while the demolition gets done and finished then would like it placed back on the wall. The only issue with this is you can not isolate that one unit with the branch box that is installed. We would need to recover all the refrigerant out of the system then remove the unit but the other 3 units will not work. Gave the estimates to the home owners for the work. She will call us when she is ready to get the work done.
Installed 2.5 ton 16 seer Amana heat pump condenser. With 2.5 ton Amana air handler with ECM blower. Drain pan with float switch, merv 11 air filter, condensate trap and drain plumbing. New ac pad and block. New line cover, lineset. All new low and line voltage wiring. All new ductwork, 10 supplies and 1 central return with 16â€ flex and 30x20 grill. Installed customer provided nest thermostat. Started and tested.
Condenser causing breaker to trip, tested compressor at terminals and found compressor no longer functional, system is a old r-22 unit, explained to customer that parts are no longer available, recommend residential replacement.
Arrived at customers home for a leak in the downstairs bathroom and to install a customer supplied kitchen faucet. Found the pop up assembly in the basement bathroom cracked causing the leak recommend replacement of the assembly. Removed old assembly installed new Gerber assembly. Checked for leaks and found the supply stops really old and leaking. Recommended replacing those as well gave customer estimate for that work. Also installed a customer supplied faucet. Removed old faucet installed new and checked for leaks. All is good at this time.
Added 2 12k wall mounted indoor units one in kitchen and one in front bedroom. New Line sets, drain lines and wiring. Started and tested Installed new MV3 in upstairs bathroom. Added 200$ to balance for vent installation New balance $4770.00
Performed annual AC tuneup on 2 systems. 2nd floor unit had weak outdoor capacitor. Replaced capacitor. 1st floor unit also had weak capacitor at condenser. Dining room thermostat was not operational. Tested units. Systems operational.
Performed annual AC tuneup. First and second floor air handler zone valves were stuck in the open position. Replaced both zone valves, motor and ball. Capacitor at outdoor first floor unit was very weak. Replaced outdoor capacitor. Tested units. Systems operational.
Installed 15k horizontal ducted air handler for 2nd floor. Supply for each room 1 central return. Wireless thermostat with red link receiver. Drain pan with float switch. Installed 9k wall mounted unit in den area above door. All new linehide, line sets, drain lines, wiring. System is charged and ready for start up and test. Ducted system needs to have receiver and thermostat linked once power is on. *electrical line voltage work needs to be completed by customers electrician*
Completed replacement of combustion blower and swirl plate. Cycled system and checked operation.
Bad blower motor and swirl plate, parts need to be ordered and replaced. Need to follow up with price to replace, currently has no heat.
Cleaned and serviced oil boiler, brushed and vacuumed heat exchanger, flue and base of chimney. Checked all water components, zone valves and circulator pump. Checked wiring. Replaced filter, strainer, and nozzle. Performed combustion, efficiency And smoke test. Tested unit. System operational. When replacing oil filter noticed filter was completely covered with rusty/mucky residue. Strainer and nozzle were also very dirty as a result of a old oil tank. Follow up needed for tank replacement.
System operational, checked pressureâ€™s, remote.
AC Tune Up on one system