Our A/C wasn't working on an extremely hot day. We called Folkes in the afternoon and they were able to dispatch a service technician within an hour and a half. Chris was very thorough and professional. He fixed our problem and we immediately had our A/C back. I highly recommend this company as they have knowledge and integrity.
Kurt takes care of my heating and air conditioning systems. Great service! I can always count on Folkes.
Danny is fantastic
System running upon arrival but not cold air being produced. Tested condenser capacitor which tested out of range, checked air filter for blockage, also checked coil to make sure it wasnâ€™t plugged. Replaced capacitor and system began cooling, also noticed system slightly over charged with high side pressure. Released some pressure and pressures tested normal. System operational and working.
Completed annual ac tune up on one system, took temperatures and pressures. Cleaned coils. Replaced on 16x20x1 filter. Cleared condensate line. No issues to report at this time. Also checked air flow coming out of vents. Did not find any issues with air flow.
Installed 10 of 3/4 copper pipe and removed a piece of board and tied loop back in,purged zone.checked for leaks and all working wel.
Performed ac tune up x2, checked all components, washed coils tested pressures and replaced filters. Replaced all IAQ bulbs and filters.
Installed Amana air handlers with Amana condenser new refrigeration pipes, emergency drain pan, Honeywell media filter, 16x20 and 20x20, new T6 thermostats, reconnected condensate pipe to existing drain, wiring as needed, new return plenum and transition pieces to reconnect to existing duct.
Completed annual maintenance on air conditioning system. With MA. Tested blower motor amps, as well as condenser and fan. Changed air filter 16x25x1. Checked all pressures and everything is operational at this time
Looked over systems, 1st floor system is empty on refrigerant, it uses r22, the second floor system is about 1.5-2lbs low on refrigerant as well. Went over the r22 issue with the customer, he would like an estimate for two replacement units.
No heat due to bad gas valve needs to be replaced. Also drip leg on gas leg not properly installed. Call to collect payment
Completed annual maintenance on ac system.
Located leak but could not locate source. Shut down house well system leak continued. Leak is pressurized and believe it may be something to do with neighbors water need to contact neighbor.
Found spill switch tripped and pilot out. On going problem with tripping spill switches. One switch failed, will not reset. Furnace next to water, pulling return air 3 ft. from water heater causing negative draft. Recommended having chimney company look at existing flue witch is only 2 ft. Off the ground. Power venter is possible, but difficult installation. Need to return and replace failed pressure switch.
Customer changes her own filter which is located inside the unit. To change the filter she has to take the bottom door off. When put back it seems the door wasnâ€™t making a good contact with the door switch. Secured the door better and the unit is operating properly. Performed gas cleaning with the maintenance agreement, found a weak capacitor. Recommended to replace it. Changed capacitor and unit is operating properly.
Cleaned and serviced oil furnace, replaced the filter, strainer and nozzle. Brushed inside and took a combustion test. The burner does need a new transformer the current one has a weak spark. Gave customer an estimate.
Water anyalysis Iron 0 mg/l Hardness 13 to 15 gpg Ph 6.8 Chroline 0 ppm Sulfur 0
Completed annual maintenance on oil boiler. Need to follow up with customer regarding duct work for stove. And need to set appointment for water testing.