Chris came to our home and assess the situation we had with a leak from our shower and did an awesome job
Once again, fixed the problem. Will never use another HVAC service. Efficient & polite.
Very promp & polite. Explained things clearly.
Was prompt and finished timely
Very responsive from moment I called until service was completed. Everyone I communicated with was professional and friendly.
Was prompt , consultative , my new boiler repair go to guy.
Chris was very nice and super helpful. He found the problem quickly and was able to immediately correct the issue.
Cleaned and serviced gas furnace. Inspected heat exchanger, cleaned flame sensor, checked wiring, capacitor, blower motor and wheel, duct, cleared drains. Replaced air filter. Performed combustion and efficiency test. Tested unit. System operational.
Customer had concerns about system running up her electric bill, Went through manufacture settings on unit, checked condenser amp draws and compared to rating plate, found draws lower then what was rated, checked running pressures, levels were normal, tested heat pump, checked electric heat strip, checked thermostat, found no issues to report system running fine with no issues, explained in details how the unit works and made some suggestions for how to run the unit like keeping it at set temps through out the home and not fluctuate temperatures. Also made recommendations for solar panels and having electrician come by and evaluating home. System operational.
Folkes arrived on 10/07/2021 for no hot water in shower. Upon arrival I tested and it was cold. I then adjusted the handle and the water was hot again. The customer was satisfied. I the. Thanked the customer for choosing folkes and left.
Folkes arrived on 10/05/2021 to mount the shower handle. Upon arrival customer stated that the screw came in. I started by cutting the screw to the correct length. I then tightened the handle to the valve and turned to make sure it turns, the customer is satisfied. I thanked the customer for choosing folks and left.
Remove condenser to have new concrete pad poured. once done reset condenser. Braze lines, pressure test and evacuate. Manager certificate- yard sign for 3 months in exchange for $200 discount 9.30.21 pumped down system and recovered refrigerant in lineset and coil. Cut and disconnected lineset and removed wiring to unit. Moved condenser to back patio.
Folkes arrived on 09/25/2021 to replace the old well tank. Upon arrival I started by turning the power off to the old well tank and disconnected the pressure switch. I then drained the house down and cut the old tank out. I then placed the new tank in place and piped everything in. I then connected the wires to the pressure switch and turned the power back on. I checked for leaks, there are no leaks at this time. I had the customer run all the fixtures in the home and they were all working. Customer is satisfied with the work that was performed. I thanked the customer for choosing folkes and left.
Found indoor blower running at low speed. Found run capacitor had failed. Replaced run capacitor and tested system running pressures and temperatures.
Installed peerless oil fired boiler with Beckett burner,all new components required by boiler installation, pipping and wiring as needed for a 3 zone valve system and tankless coil, installed mixing valve.
Service for leaking well tank arrived to find that well tank tee was leaking. Customer stated it was replaced one before. Explained to customer how this wa a special order tank tee and the was no guarantee if plastic connections were broken on tank while installing new tee. Explained customer best option was to install new tank. Customer went ahead with work we will return tomorrow.
Hot water coil on oil boiler is plugged. Coil needs acid flush. Collected deposit, Following up with office to coordinate our return to do the acid flush.
Found broken wire going from gas valve to temperature sensor breaking voltage to gas valve causing system to not light, re connected wires and re lit pilot and system fired right up, let run for 20 minutes no error codes at propane gas valve and customer should have hot water in 45 minutes.
Completed annual maintenance on air conditioning system. Tested all components and pressures everything operational and working. Also cleared clogged condensate trap.
Replace well tank inside home. Install new tank tee and pressure switch. Service for well tank installation: arrived to home to go over scope of install. Shut off power to well tank and removed wires from pressure switch. Removed old tank and tank tee. Installed new tank with new tank tee and fittings. Piped in unit and turned on well pump and checked for leaks all working properly at this time. Customer is satisfied with service. All working properly at this time.
Replaced boiler spark ignition module for one gas boiler, tested operation, boiler fired up let run until boiler got up to temperature
Arrived and found the boiler off. Turned the breaker back on and found the inducer motor running but not the burners. Found the spark ignition mealie bad had 24v to it but nit sending power to the gas valve. Gave pricing but the customer doesnâ€™t have the money right now. He is going to the bank Monday and will call when he has the money for the part.