needed a cracked pipe replaced and one of there techs came out right away, very friendly and knowledgeable. fixed it on the spot, no going back and forth for parts like some other plumbing companies. 5 star service at its finest.
Arrived at customers home to do a complete free whole home plumbing inspection.
Found system running in call for heat. One tenant had thermostat set for 80F. Checked operation of hot water working normally. Found faulty general heating pump, when call for heat boiler is overheating. Sent customer estimate for repairs. May replace pump himself.
Arrived at customers home for a issue with kitchen stove possible gas leak. After evaluating found that stove needed to be converted to propane as itâ€™s currently set up for natural gas. Left gas off.
Found relief valve leaking, replaced along side with Air vent, checked temperatures, pressures, also found air in water line for indirect hot water heater, purged, tested, system operational. Recommend calci flush done on boiler.
Arrived at customers home to inspect a leak underneath trailer. I cut installation back and inspected where the leak could possibly be coming from I noticed that a 3ft section of the pipe had a crack. I cut out the compromised section of piping and replaced it with new piping. Turned on main water and checked for leaks which there wasnâ€™t. Everything was in working order on departure.
Completed annual maintenance on one triangle tube boiler.
Water leak at relief valve caused by bad expansion tank, recommend to replace, along side with 1/8 Air vent