I called to verify temperature reading from the thermostat on the wall, and without delay they sent a technician to review my question and i was very satisfied following his checking.I find things handled very professionally.
Great technician came the same day we called, was very polite and knowledgeable.
We are very pleased with folkes , from the first installation to the service . All of the guys that have been in and around our hone have been nothing but courteous and respectful. Thank you
Good job. Happy with the tech and service
Many times you never know what your really getting when you hire service to be done, weather in or on your home, and that can also be applied to your automobile. With that being said, our experience with 'Folkes' was more than we expected. From our initial contact to the finish, was pleasant and comfortable. Your Tech.Deago and helper were as professional and courteous like I have not witnessed in a LONG time.
The 2 service techs were polite and worked quickly to service my furnace. Nice gentlemen.
Knowledgeable person n explained n answered all questions
A great company to use. There was a small issue after my first install and they sent Niheem right back out and he fixed the issue promptly. I would definitely use them again.
Found bad capacitor at condenser, replaced, tested, system operational.
Called out to trace a vent line. I went on the roof to find the vent and there is no vent on the roof. I left an estimate to install a fresh air vent in the basement to the exterior wall of the house. If the customer decides to move forward with the repair, we will credit the diagnostic fee from today and also subtract $150 from the total.
No ac due to bad contactor, replaced, tested, system operational, recommend maintenance on AC.
Called out for a clogged toilet in the first floor. I used the auger to help open the toilet trap. That didnâ€™t help so I replaced the toilet and when I flushed the toilet is still backing up. I installed a temporary vent and we will come back to check the venting for the toilet. Erica 8453329743 Hopewell septic is the name of the company that did the work.
Found bad contactor, replaced, also system low on r-22, charged, system operational. No charge as per DJ due to customer replacing AC next week.
Estimate to install ductless heating and A/C and water heater. New customer. Joe is the decision maker.
Found system low on charge, added r22, checked over entire system. operating properly. the customer is replacing the system, they have an estimate set for 3pm today. Customer will be credited for the refrigerant.
Checked pressures and temperatures. Delta t is 26 degrees. Pressures are perfect. Checked filter. Checked both coils. Everything is operational. No issues found at this time.
Customer was given pricing to cut down 30ft of insulation to inspect one supply run of duct work. Inspected main supply and nothing was disconnected or had holes in it. Customer wants to get a quote for re-insulating the underneath of the home before we take down any
Found compressor not energizing. Electric fault in dual run capacitor. Also found contactor burnt and pitted. Replaced capacitor and contactor. Checked system running pressures and temperatures. 71/267psi, superheat 25, sub cooling 9.
System very low air flow when using ac. Normal airflow using heat. Attempted to go under home to inspect ductwork. Dead animals need to be removed before inspection. Checked coils, blower, filter and took pressure readings. Running pressures 135/441, superheat 0, sub cooling 44+. System has been overcharged. Air flow still main issue. Customer will let us know when weâ€™re able to get under home.
Adjusted settings on thermostat, heating and cooling is operating normally.
Completed annual AC tuneup on one system. Cleared drain and trap lines. Replaced one 20x25x1 filter. Took temperatures and pressures.
Found new thermostat installed but needed a c wire. Customer just wanted a regular thermostat. Installed a new thermostat and unit is operating properly.
Bled oil line, tested, system operational