good friendly service.
Greg is great person and very patient with tech support to trouble shoot thanks
Was very helpful and professional. Great experience working with Troy to find out the right system for my home.
Response from Folkes Heating, Cooling and Burner Service:
That's what we like to hear. Thank you!
I was well informed as to what was needed and how long it would take.
Pump down compressor, Installed drain pan for Evaporator Coil, tied in new ez trap, pressure tested, pulled vacuum, tested, system operational.
Checked all components, pressures were good, delta t was at 14, filter is clean along with the coil. The system is older and will only maintain temperature in the house. The customer will think about replacement after this summer.
Found water leaking out of air handler into emergency drain pan. Found crack in drain pan. Also found cracked drain trap. Need to follow up with customer with pricing and availability to replace pan and trap.
Found clogged drain line, cleared, tested, system operational. One room on 2nd Floor not cooling properly, removed dampers, customer found leaks in ductwork, customer stated he will seal duct work, gave customer 5 36inch zip ties.
Found clogged air filter, removed, also found no plugs on 1st drain pan, plugged, removed water from secondary drain pan, tested, system operational.
Completed replacement of compressor and electronic expansion valve. Pressure tested, evacuated and recharged system. Checked system running pressures and temperatures.
Referral from Gad (company). Looking for estimate for heating and cooling system. Electric home. Single family home. Does not currently have central air.
Estimate for heat pump system. Single family home - Oil system for heat - Currently has central AC.
Duct board coming off supply duct, tape came undone. Retapped supply plenum and made sure all ducts were connected. The back bedroom is also the longest run in the house. Air flow better than what it was upon arrival.
Installed PCB board and condenser fan motor. Started system. Locked out on compressor over current fault. Manufacturer requested to remove charge and weight in proper charge as system was not charged properly by previous company. Still get fault. Recommended to replace compressor. Need to get pricing and availability on compressor replacement.
Completed annual ac tune up on one system. Replaced 16x25x4 customer supplied. Installed fm2 uv light. Cleared drain and trap lines. Took temperatures and pressures. Need to schedule duct cleaning. Duct cleaning paid in full.
Checked operation of all three zones. Found cover for zone valve on top of boiler. Put on zone valve. System operating normally. Found 50 gallon electric water heater leaking. Took information and quoted customer for replacement. She will call with decision.
Air handler and condenser running upon arrival but no cold air coming from vents. Tested capacitor on outside unit and found capacitor almost dead. Replaced capacitor and tested system.
No cooling on ductless heat pump. Spoke to manufacturer. Determined outdoor fan motor and PCB board need to be replaced. Parts need to be ordered, still under manufacturer warranty. Quoted customer for labor. Any further repairs beyond replacing warranty parts will be chargeable.
1 A/C renew