Checked air filter, duct work, Evaporator coil, found smell coming from just kitchen, living room, and dining room. Recommend having crawl space evaluated. Smell not coming from AC. CC on file
Fan left on the on position with no AC just fan continuing to run. Cleaned inside unit and coil where air passes over and sprayed cleaner down each vent. Also air box door left off or fell off causing air to be sucked in from crawl space which is the same musty smell throughout the house. Sealed unit. Also water leak from clogged trap cleared line and tested.
Arrived at customers house for possible recall on a clogged kitchen sink. Found sink still clogged gave customer options and decided they would let us know if needed us to snake the drain again.
Called out for a clogged kitchen sink drain. After snaking approximately 50â€™ into the drain I removed a sanitary wipe which probably came out of the main sewer. The sink is now draining properly. Cleaned up and collected payment.
System operational, found clogged air filter, replaced, tested, system operational.
Replaced motor, tested, system operational. Call landlord to collect payment
No AC due to bad blower motor, need to order and replace for unit to be operational.
Performed annual maintenance on air conditioning system. Changed one Merv filter 20x20x4. Installed one UV light system. Cleared condensate drain lines. Tested blower amp reading which was normal. Changed return filter in living room 14x30x1. Tested pressures at condenser which looked normal. Tested capacitor which was normal. Brushed outside coil. System operational and working at this time. .
Found r22 system low on refrigerant. Recharged system. Advised customer of r22 phase out. Declined free estimate at this time.
Found collapsed return duct in attic not allowing any air across coil system freezing up. Put in a follow up form for us to give the customer a quote to repair it.
Arrived at customers home for complaint of leaking tub spout customer change cartridge and advised me that still leaked took half deposit on shower valve replacement with chrome trim and new tub spout. Also need to replace ball valve for hot water to shower valve.
Call back, common wire came off capacitor, was not properly secured, adjusted, tested, system operational.
Completed annual maintenance on ac system. Customer renewed maintenance agreement for one year.
Arrived and found boiler leaking into an overflowing bucket. Shut water off to boiler and closed all valves. Drained boiler down a little but to stop the leak. Found a bad expansion tank, relief valve, air vent and sure temp gauge. The customer would like to wait on repairs as he wants other prices. May think about replacement. He said he will call back to let us know in the morning.
Found watts mixing valve sticking need to replace got it working temporarily will call with price to replac3 tomorrow