I have already given the name of the company to a friend! I am Very impressed !!
Found end cap of supply duct disconnected where two back bed rooms were not getting cool. Remarked end cap and taped over back bedrooms have much better air flow, took a temperature difference of supply and return air and got a difference of 16 degrees. Also checked pressures which were normal. Mail invoice to customer.
Arrived at customer home and found cold water on new faucet not flowing.troublshot faucet and found lines installed improperly on manifold.reinstalled lines and faucet is working properly
Found system low on charge, gave customer option for leak search or recharge. Customer wants to recharge it to have it working now. Customer was under the impression of getting the diagnostic fee back.
Found coil frozen upon arrival. Customer replaced filter yesterday. Need to come back tomorrow after 6 pm to further diagnose issue. Diagnostic fee was payed in full today on 6-11-20
Called out to install a customer supplied shower head. After speaking with the customer regarding the replacement of the shower head I gave an estimate to install. I cut a small hole in the Sheetrock behind the shower stall and removed the drop ear elbow. I reconnected the shower arm and head. There are no leak at this time. Cleaned up and collected payment.
Called out for running toilet. After checking the flapper I noticed the flush valve was dripping. I removed the toilet tank from the bowl and replaced the flush valve. I then opened the water to test for leaks and flushed several times. There are no signs of leaks at this time. Cleaned up and collected payment. The work done here today has a one year warranty.
One year old system not cooling. Found thermostat mis wired causing low voltage fuse in furnace to blow. Rewired and replaced fuse. Checked system operation. Refrigerant levels. Slightly low. 117/256psi, superheat 29, sub cooling 2, temperature differential 15. Recommended getting refrigerant levels to manufacturers specifications. Customer will wait on charging system.
Called out for a toilet that wonâ€™t fill. After speaking with the customer regarding the toilet tank flapper. I removed the old flapper and installed a new fluid master flapper. I opened the water to test for leaks. There are no leaks at this time. Cleaned up and collected payment. The flapper has a one year warranty.
Called out for a leak under the kitchen sink. After speaking with the customer regarding the leak I gave estimate to install a shut off valve and install a customer supplied kitchen sink faucet. Both were installed properly although the side sprayer is defective and must be replaced. The work done here today has a one year warranty.
Estimate to install ductless for heating and cooling. New customer. Onal and Melvina will both be present.
C/S Oil, Renewed MA, Replaced expansion tank, air vent & ignition transformer. Purged, tested, system operational, also replaced, electrodes and oil burner motor. Recommend to have chimney cleaned.