Works hard and fast which gives him more time for the up sale.
Happy with the service
Performed the air conditioning tune up. Cleared the drain, cleaned the evaporator coil and changed the merv 11 air filter. Outside I checked the pressures and electrical components. No issues to report. The system is from 2018. Washed the outdoor coil with the garden hose. Starting to see some dust and dirt build up around the vents. Mentioned a duct cleaning to the customer.
Arrived and the customer stated the condenser was running but inside was not cool. Found the compressor running but not the fan on the condenser. Found the capacitor for the fan bad. Replaced and tested the system. The customer is moving out of the home and needs it working right now.
No ac. Found vents covered with rugs through out home. Uncovered vents and was getting a delta t of 10. R22 unit, checked filter, filter was good. Checked pressures low side was 58, attempted to inform customer of situation with r22 and how I can add the refrigerant but there is no guarantee on it due to no leak searches for r22 unit. Customer does not speak English and was not able to comprehend what I was attempting to describe. He ended up deciding on holding off.
Met with duct tester. We did pass on both systems
Installed surge protector at disconnect box outside by condenser. After installing, tested and all 3 Leds on surge protector are green meaning surge protector has been wired correctly and working normally. This was owed under new install
Install air handler in attic with 9supply and one return in hallway 24by30 grill set condenser outside in back yard run brown line hide with line set and condensate drain line is run in cutter in the back yard al hole are Caulk up. Customer pointed out to me that there should be a surge protector install on Equipment but none was provided so the office should reach out to me to set up something their is a balance of $7066.78
Heat pump tune up x2 with 1st year install, Also checked high efficiency boiler, customer has issue with domestic hot water, found mixing valve not working, replaced, tested, system operational.
Cleaned and serviced oil boiler, replaced the filter, strainer and nozzle. Brushed and vacuumed inside of heat exchanger. Took smoke and combustion test. No issues to report.
System operational no issues, adjusted thermostats, tested.
Found the thermostat not calling for heat, jumped out the themrostat and the system worked. Customer does nit want the repair done, they will changing themselves.
Performed AC tune up. Cleaned inside coil, cleared condensate drain trap, took blower wheel amp readings which were normal, inspected duct work which looked good, took temperature readings of supply and return air and had a difference of 18 degrees which is good, changed return filter 20x20x1. At condenser tested pressures which were normal, tested capacitor which tested in range, contactor in good condition, all wiring looked good, washed outdoor coil with hose not very dirty. System operational and working.
Performed dryer vent cleaning, removed flex pipe and cleaned with vacccum and ran vacuum to outside vent. Recommended to sign up for heat and ac Ma. Customer believes she is still under contract with company who installed system, house is only a year old. She will speak with her husband and if not under contract will call office to sign up.
Called out for a shower temperature issue. After speaking with the customer regarding the temp issue I gave an estimate to replace the delta shower cartridge. The customer declined the estimate and the landlord will do the job. A diagnostic fee was collected.
Completed annual maintenance on oil boiler.
Cleaned and serviced gas boiler, took all burners out including pilot assembly and cleaned them. Took gas pressure reading along with combustion and efficiency test. All readings looked good.