Greg was wonderful and diagnosed a problem with our furnace that hadn’t been brought to our attention before. I’ll definitely follow up on his recommendations.
Install regal oil furnace with burner to exciting duct work program t6 thermostat and explained to customer how it works
No AC due to bad capacitor at furnace, replaced, tested, system operational.
Found a crack on drain line, recommend to have line cut and repaired, customer declined repair, flushed drain line, checked pressures, system operational.
Boiler not running upon arrival aqua smart aquastat on hard lockout tried resetting aquastat and right to hard lockout replaced customer supplied aquastat probe and boiler fired up no codes. Could not run boiler long due to water supply line cut customer will have to cap that line due to water heater feeding boiler. Also noticed all three zone valves will need to be replaced all frozen due to water damage, air vent is leaking, customer will look into getting parts and have us install them.
Found burner burning poorly. Over a year since last maintenance. Completed annual maintenance on oil furnace. Found blower motor struggling on start up, running very slowly causing furnace to cycle on high limit. Recommended replacement of blower motor.
No AC due to system completely empty on r-22 recommend residential replacement.
Clean and service Oil with MA, replaced transformer and cad cell eye assembly, tested, system operational.
System operational, needs maintenance but can wait till January for Cleaning.