The technicians fixed the issue and I’m satisfied. Thank you Folkes.
It was a pleasant experience.
My experience was good
Tech Danny gave great service
Found condenser fan not spinning. Replaced capacitor. Tested operation. No further issues to report at this time. Ac is now operating normal.
Took measurements and pictures of duct work
Repipe under bathroom sink and add air vent,also repipe and add air vent under kitchen sink.returned to customer home and installed air vents under sinks.reconected plumbing tested functions all working well
Pull toilet and snake through toilet cleared line and all working well
Arrived at location land lord tenant.found both sinks not vented.gave landlord sal estimate to install air vents on both sinks.sal will call office to put deposit down or pay the service fee.
Completed annual maintenance on one system. Cleared drain and trap line. Cleaned both coils. Replaced on 20x30x1 filter. Took temperatures and pressures. System low on charge. Recharged r22 system. No further issues to report.
Performed Ac tune up. Cleared trap and drain line. Checked evaporator coil, indoor blower, capacitors, delta t, thermostat, pressures, contactor , capacitor, fan and compressor. System is operating normally.
No AC due to emergency switch turned at top of stairs, turned back on tested, system operational, as per Dustin no diagnostic charge.
Arrived at customers house for a clogged toilet. Cleared toilet.
Ac Tune Up, mail copy of receipt to customer
Customers disconnect switch was not in fully. Push in and system started up. Took delta T and customer is getting cold air. Customer stated that she would like the contact info to be under Bridget Garmon she is the homeowner instead of Hewitt Taylor who was her brother who scheduled the appointment for her. System is operating normally.
Performed ac tune up.
Found primary drain pan overflowing due to restricted drain line. Cleared drain and checked drainage with water. No emergency drain pan with original installation. Donâ€™t believe we would be able to get one in now, restricted space. Need to call customer to schedule maintenance appointment.
No AC due to bad capacitor, replaced, tested, system operational.
Found outdoor condenser not energizing. Disconnect fuse was blown. Replaced 30amp fuse and checked system operation. Checked running pressures and temperatures. Replaced air filter. Condenser is 32 years old and in poor condition. No guarantees, recommend replacement. C.C. on file.