Very Professional thanks
Completed annual maintenance on one gas furnace, changed return filter 16x25x1, cleaned flame sensor, cleaned burners and inside burner box, inspected heat exchanger which no signs of cracks, tested capacitor which tested in range, tried to fire furnace and gas valve opened but igniter didnâ€™t glow, pulled igniter and found very worn and a crack in middle rod, replaced with new igniter and system fired right up, took combustion test which everything looked normal, 70 degree difference in temperature, system operational and working,
No heat due to bad thermostat, replaced, tested, system operational.
Removed existing American 40 gallon natural gas water heater. Replaced with new Bradford white 40 gallon natural gas water heater. Made all water line, gas line and venting connections made sure all secure. Also installed spill switch on water heater to code. Water heater Bradford white 40 gallon Model # rg240t6n Serial# wb44734350
Hot water heater leaking need to be replaced
Cleaned and serviced gas furnace, replaced the filter and checked electrical components.
Completed annual maintenance on gas furnace. Tested pressure switch, flame sensor, capacitor, inducer, and blower motor. System installed 2 years ago, system is operating normally. Customer is interested in signing up for maintenance agreement but would like to have the pricing emailed to him so he can sit down and go over it.
Replaced furnace high limit switch. Took temp rise readings. Supply temperature around 135. Replacement filter.
Wrong part. Need to return when correct part comes in.
Bad limit switch causing issue, recommend to have replaced, under warranty, system installed in 2017