Professional, very polite and well spoken
Greg and Chris out our mind at ease. Their opinion coordinated with our opinion
Scott was polite and very thorough
Called out for a leaking toilet. After speaking with the customer regarding the running toilet I recommended replacing the kohler toilet tank seal. I went to pick up the seal and installed. There is no sign of leaks at this time. I also changed the house filter as requested by the customer. Cleaned up and collected payment.
Recharged ac system with two pounds of r22. Tested system took temperature at vents. All tested fine at this time.
Customer stated they got the thermostat working correctly and programmed the way they want. They had downloaded manual from online.
Ac Tune Up, schedule appointment for residential replacement.
Found furnace locked out due to blower not energizing. Found failed capacitor. Replaced capacitor and checked system operation. Maintenance to be done in the fall. Door switch was also broken, bypassed. Need to see if available to replace switch.
Called out for a plumbing inspection. I inspected all three bathrooms and kitchen and found no issues. All plumbing is new as they recently bought the property. It is recommended to install a water softener although we would need to find a suitable place to install it as there isnâ€™t any room for it in the mechanical room.
Completed annual cleaning. Cleaned blower cabinet. Checked inducer, blower, heat exchanger, pressure switch, flame sensor, hot surface igniter, control board, thermostat, drain line, and filter. System operational.
Performed tune up on gas furnace. Checked, heat exchanger, burners, pressure switches, safety switches, gas valve, flame sensor, drain line, inducer, blower motor and wheel. System operating normally. Customer signed up for Gas, AC, and Plumbing MAâ€™s
Performed cleaning on gas furnace. Checked flame sensor, pressure switch, capacitor, heat exchanger. System operating. Drained water heater. Customer is interested in duct cleaning. Sent customer estimate and e would like to go over pricing with wife
Clean and tune gas