Folkes listed you my problem, sent a technician over why quickly identified and solved the issue at hand. Great work!
Chris was great. Very helpful and knowledgeable while also very polite
Friendly, reliable and trustworthy service.
My only criticism is that every time, there's always something suggested that would cost approximately $1000 - which is partly because my house and equipment are not new but it's also disappointing. The service is great, however!!
Job well and professionally done. Great service visit. Good manners. Task at hand completed in good time.
Found the blower motor spinning a slight amount then stopping and stuttering and continuing that sequence. Blower always has power to it, it is bad and will need to be replaced. Non stock product
Installed spill switch and tested system. System operational.
Condenser fan motor turned on but not compressor, checked the capacitor and the compressor side was at .714 out of 25. Replaced and tested system. System is now operating properly.
Clean and service Oil
Electronic air filter no secured properly in return vent flopping around. Installed a couple screws to hold it in place, also removed Merv filter by unit getting a restriction because of electronic filter and Merv filter.
No leak, customer had her neighbor make the repairs, checked trap, drain line for AC, Air filter, system operational.
Performed ac tune up. Checked pressures, contactor, capacitor, delta t, replaced filter, checked condensate pump, cleared trap, checked blower whee and evaporator coil. System is operating normally.
Found piece of plastic in blower wheel making screeching noise. Removed plastic and noise went away. System operational and working at this time.
Called out to install a 40 gallon water heater. We drained and removed the old tank. We then installed a 40 gallon natural gas atmospheric water heater with spill switch. I was unable to get the pilot to stay lit. We will come back out monday to lite the pilot. Model # g6240s40r400 Serial #2027120003418
System frozen over due to bad blower wheel in air handler. Customer would just like estimate for residential replacement.
Performed AC tune up on one system, changed return filter, cleaned inside coil, tested capacitor and cleared drain line. At condenser noticed my pressures were very high and coil completely plugged with dirt cleaned coil and pressures improved. Tested capacitor which tested in range, contactor in good shape. System operational and working. Please mail invoice to customer.
Found system operating normally upon arrival. Delta t was 19 degrees. No error codes on led diagnostic panel in condenser. Customer states he will replace filter himself. Coils are clean. All electrical components are good. No issues were found at this time. Customer states ac came back on a few hours ago. House was to set temperature at this time.
No leaves and no noise
Completed annual tune up on two systems. Upstairs system operating normal. Delta t is 19 degrees. Pressures temperatures and amp draws are normal. Thermostat for both floors were off upon arrival. First floor condenser was not turning on. Found disconnect in the off position. Then turned disconnect to the on position and then found breaker panel inside kept tripping. Pulled disconnect back out and breaker was still tripping. Breaker panel sparked and gave a small amount of smoke coming from inside breaker panel. Turned of breaker for ac unit and called ds electric with customer. Customer states sheâ€™s had a power outage on June 25th 2020. She said ac has been working all summer except for today even Though the disconnect was in off position. It is physically impossible for system to have been running. Also condenser fan was covered in cob webs.
Arrived at customers house to install new electric hot water heater and replace existing water softener. Made all water line and electrical connection to both units. Also ran drain line to stand pipe in laundry room. Started and tested both units. Checked for for leaks And removed old units. Also replace diverter valve cartridge and trimmed out valve. Tank info American Model # e6n-40r 110 Serial# 2025119778358