Respectful and thorough employees.
Professional and informative.
Thorough job estimating my repairs. Worker was conscientious and respectable. Answered all questions I asked.
Scott was very courteous and Professional at All Times
He was very knowledgeable very courteous I was very pleased with his service you guys are great
Zack a excellent worker. Very professional. He saw the problem & fixed it right away. Very mannerable young man.
Cleaned and serviced one oil Boiler, vacuumed combustion chamber and around boiler, inspected chimney flu which was clean, changed filter, nozzle, and strainer, bled oil filter housing by tank, cleaned burner head which was very dirty, cleaned and inspected burner tube, tested two zones, air vent good, expansion tank good, wiring in aquastat looks good, bled oil line, performed combustion and efficiency test which had to make a slight adjustment to air band system running a little rich, system operational and working. Customer took out maintenance agreement for one oil system.
Estimate for shower drain: Arrived to customerâ€™s home. Customer led me to bathroom that is being renovated. Customer wants their drain to be in the center. Customer says they will install the base and hook up the drain in the end. Asked the customer if theyâ€™d like anything else to be move or re done. Gave the customer an estimate. Customer says they will think about it. Emailed estimate to the customer.
Cleaned and serviced gas furnace. Checked the entire system, no issues to report. Noticed there was not a humidifier on the system. Went over this with the customer. She is not interested at this time. Left an estimate and emailed it. System is operational.
Service for running faucet: Arrived to customers home. Faucet on bathroom sink was running. Faucet is in good shape. Took handle off and checked stem. Did not have a stem for this faucet, faucet did not have name brand printed. Gave the customer a price to repair the faucet handle. Customer agreed and I proceeded. Turned off the water. Replaced the washer in the stem. Put handle back together and tested for leaks. Faucet is working properly. Asked the customer if theyâ€™d like a water quality test but declined. Asked the customer if there was anything else theyâ€™d like me to check. No more issues at this time. Customer was very happy with the service. Paid with card.
Arrived to the home and found after dripping from the cold side going into the boilers plate exchanger. Replaced the Oâ€™ring inside the union and the leak stopped. Found that the customer had hard water. Gave an estimate for a water softener. The customer is going through with the water softener and we will be installing it soon.
Cleaned and serviced gas furnace. Inspected heat exchanger, cleaned flame sensor, checked capacitor, blower motor and wheel, duct, replaced customer supplied Merv Air Filter. Performed combustion and efficiency test. Tested unit. System operational.
Cleaned and serviced gas furnace. Inspected heat exchanger, cleaned flame sensor, checked wiring, duct, capacitor, blower motor and wheel, and discharge pump. Replaced air filter. Performed combustion and efficiency test. Tested unit. System operational.
Cleaned and serviced gas boiler. Cleaned flame sensor, cleared drains, inspected wiring, expansion tank, 2 zone valves, water feeder, backflow preventer, air vent, and relief valve. Performed combustion and efficiency test. Tested unit. System operational.
Price includes no financing which is an option Dug down ground to 18 inches, laid down the 20ft of poly gas line in the ground and put a shut off valve at meter bar and on the other end of the pipe on the riser. Pressure tested and held pressure at 24psi. Piped hot and cold line to the tankless water tank. All thatâ€™s left is to run electric, fresh air / exhaust with condensate pump, also needs to finish piping the gas line to the tankless water heater.
Service for Camera sewer line and re pipe: Arrived to the customers home. Talked with Dan about what Iâ€™ve done the last time I was there. Dan sent camera throughout the sewer line and found obstructions and debris. Took photos and recorded what we saw. Dan gave the customer estimates for the work that needs to be done. Told the customer that I will need to go to the supply house to purchase material. Came back and gave the customer time to use any fixtures before I started removing the old waste line out. Started by supporting the 3 inch vent going straight up with wood and band iron. Pulled toilet out. Carefully cut out waste line. Started re piping for toilet, drain for tub/ bathroom sink, and drain for kitchen. Installed a wye with a clean out. Supported waste line with green field straps. Re set toilet with new wax ring, Johnny bolts, new toilet supply line. Tested for leaks, ran all fixtures at the same time several times. Added a bead of silicone around the toilet. Cleaned up a
Replaced blower motor and control board on furnace, tested AC & Heat, system operational, recommend maintenance on furnace
Customer is looking to possibly install nest thermostats in the future. Confirmed on two of the four thermostats they do have the proper wiring to install a Wi-Fi thermostat. Included estimate for install.
Cleaned and serviced gas furnace. Inspected heat exchanger. Cleaned flame sensor. Checked wiring, capacitor, blower motor and wheel, 2 zone dampers, and replaced air filter. Performed combustion and efficiency test. Tested 2 zones. System operational.
Service for water leak: Are to customers home. Customer says waste pipe is leaking and it can be seen from the basement. Took a look at where the water leak was. Leak was behind wall. Used a camera to look behind the wall. Told the customer that a section of the wall must be cut to find the leak. Cut open wall and found the leak on the pipe. Gave an estimate to replace a section of pipe and agreed with the price. Started cutting the pipe in 3 places to be able to get out of the wall. Tried to pipe in new pipe it in 2 pieces but it was very tight. Joe came out, and suggested to pipe in new waste pipe with 45 elbows. Piped in ne waste pipe and secured all fencos. Tested for leaks. Waste is leak free. Installed new fill valve provided by the customer, flapper and toilet supply line. Adjusted water level. Did not charge for toilet repair. Installed 1 1/2 gym cap on laundry drain, since itâ€™s eliminated. Took a check for the charge #316 and did check capture. Customer would like a paper r
Customer has very little air flow in master bedroom close to none, said problem has been like this for awhile, they are trying to sell home, found damper slightly open for supply run also supply run for master bedroom is longest in the house, customer has a electronics air filter on system and suggested putting a thinner filter in unit due to furnace being belt driven and needs as much air as possible, also suggested duct cleaning as well hasnâ€™t been done in years could remedy the situation, you canâ€™t see full length of supply runs they go through the walls so itâ€™s possible something has come detached. Customer will try filter first and see if that works